Casey became a service technician at Hyde’s over 6 years ago. He worked in the HVAC business for nearly 16 years and is NATE and EPA certified. When he’s not fixing broken air conditioners, Casey enjoys classic automobile restoration and golfing. Casey advises customers to “be proactive when it comes to your air conditioners and don’t get stuck in the hot summer without it.”
Name: Casey Harrison
David - La Quinta, CA
Exemplary service from Hyde’s as always! Casey was professional personable, and knowledgeable.
Excellent service Casey was on time and did the service in a timely manor
Bob - Indio, CA
Serb above comments
Excellent service by Casey
Moira - Indio, CA
What a lovely fellow Super nice and very knowledgeable .
Found drywall dust in the thermostats, the renovation was done about 6 years ago!
Richard - Palm Desert, CA
Very comfortable experience
Florence - Palm Desert, CA
Very pleasaed to have your company keeping my AC's in working order.
great service. great information
Sharon - Palm Desert, CA
two impressive guys. look forward to installation
Henriette - Rancho Mirage, CA
Everyone at Hyde AC has provided top notch service. Thank you
miss leading pricing
Gary - Palm Desert, CA
Brian - Palm Springs, CA
John - Palm Springs, CA
Casey knew what he was doing and explained everything.
Performed heater service on 1 system. System within man. Spec. 16x30,14x14. Recommend replacement. R22 system.
Performed heater service. Both systems within manufacture specification. Replaced both filters and recommended whole home surge protection.
Performed heater service on heater and 2 ductless. Guest house unit not operating properly. I told client we would go thru it in the spring.
Performed heater service. System operational. Found wrapper in blower throwing off balance of blower, Removed wrapper and lowered fan speed.
Performed ac service on 2) 20 year old York package units. 2.5 tons ea. Replaced all filters. STD lakes filters. Temperature split 67Â°return 47Â° supply on both systems. Static pressures within man. Spec. Both systems are beyond life expectancy and do run on r22 freon.
Performed service on 1 package unit. Filter is 24x25. System is 17 years old and living on borrowed time. Made client aware that California regulations are forcing up cost. Also system runs on freon which was phased out Jan 1st 2020. Highly recommend replacing system.
Performed heater service on 3 systems. Equipment is operational but at the end of its life expectancy. Systems use r22 which has been phased out.
Performed heater on 1 hp split. System operating within man. Spec. 20x25 filter.
Dropped book collected paparework.
Performed heater service on 2 systems. Both heater operational. Lowered fan speed for main home system. History notes said refrigerant added last year 2 lbs. 410. Outdoor unit replaced in 2015. Made client aware evap. Coil was not replaced at the same time. Gave option to replace coil and refrigerant to clean out system.
Performed heater service on 2 package units. Both systems are within man spec. STD lakes filters.
Performed heater service on both systems. Replaced both filters.20x30,14x24. Both systems operational but beyond life expectancy. See previous debris for recommendations.
Dropped Barryâ€™s book
Dropped book for Barry
Performed heater service on 1 system. Found system operational. Rewired system to not need batteries.
Performed service on 1 hp system. Out in September and did note restriction. Todayâ€™s ref4igerant levels are within man. Spec. I let them know theses things some5imes resolve them selfs so no need to order part. Letâ€™s reevaluate in the spring. Told to call in May.
Performed heater service on 1 system. Found the heater operational and replaced filter. 16x25. Looks like client had chuck in a truck install 410a condenser on r22 coil.
Heater service 2 units in garage. Systems are 20 yrs old. I have talked to client about replacing equipment before and I brought it up today. 14x25,16x25
Performed heater service. Package unit. Marked unit 251. System operational. 20x20 filter
Performed heating service on 1 system. Dialed in airflow. Replaced filter. Set up low heat and cooling fan to 1600 cfm in high cool.
Pulled blower and cleaned. Also sprayed down coil with no rinse coil cleaner. Upon checking operation of the ac I found low voltage to main power. Upon checking panel found low voltage at the main breaker. When I went to reset main it would not. Client is calling his electrician.
Performed heater service on 1 system. Package unit on roof. System 2006 model and uses r22 freon. Made clients aware of age and regulations coming.
Performed heater service. Living room system older. Made client aware of freon phase out and the scaqmd regulations combing for package units.