Casey became a service technician at Hyde’s over 6 years ago. He worked in the HVAC business for nearly 16 years and is NATE and EPA certified. When he’s not fixing broken air conditioners, Casey enjoys classic automobile restoration and golfing. Casey advises customers to “be proactive when it comes to your air conditioners and don’t get stuck in the hot summer without it.”
Name: Casey Harrison
Seasonal HVAC Check up and Tuneup
Joel - La Quinta, CA
As always, Hyde's provides outstanding service, professionally delivered, by a customer-centric team.
An Absolute Professional
Conn - Indian Wells, CA
The Hydes technicians are amazing. On time, helpful, explain anything that I ask about, and do a great job. I’ve been thoroughly pleased with every aspect of their service.
Jim - La Quinta, CA
Casey is very good
Noreen - Palm Desert, CA
Beverly - Indian Wells, CA
Casey is Great!
Cynthia - Palm Desert, CA
Casey is always professional and does a great job.
Thanks for the unexpected gifts. Very thoughtful.
Connie - Palm Desert, CA
Your company should be very proud to have Casey as your employee. Casey’s expertise and knowledge to help his customers understand the process and workings of your products. I’m positive that he made all the right choices for me to enjoy desert living in both heating and cooling of my home. Thanks again Casey. You are the best!
Response from Hyde's Air Conditioning:
Casey is awesome! Thank you for recognizing him!
Fantastic and personable company
Sam - Indio, CA
Casey Harrison has been our technician for 2 years. Excellent, outstanding employee. Listens to any concerns and explains everything to us to our satisfaction.
David - Indio, CA
Knowledgeable tech and very personable.
Carrie - Indio, CA
Casey was excellent nice young man very thorough thx
Performed heater service on 1 System. System within manufacture specifications. 20x25 filter.
Performed heater service on 1 system. Found system operational and within manufacture specification. 20x30,16x30
Blown transformer. Client replacing systems.
Loose disconnect. Also fixed wiring outside at condenser that probably was the initial cause of short.
Performed heater serivce on all 3 systems. All within manufacture specifications. Replaced all filters.
Ductless leak at flare indoor coil.
Performed heater service. Both system operational. System on east side has 1992 furnace. Cleaned burners and compartment.
Performed heater service. Filter clean. System 12 yrs old made client aware of age and life expectancy.
Called cient, mail box full
Client has wireless device we were just out to install compressor. I came back to recomnect wireless controls.
Performed heater service. Found heater within manufacture specifications. Washable filter. Vacuumed closet and furnace. Recommended panel tune up.
Performed heater service on 2 systems. Both systems operational. Washed filters and vacuumed closets and furnaces.
Performed heater service on one system. Operational. Clients aware of age. 36 yrs old. Recommend replacing system before scaqmd rule 1111 heater regulations. Also next yr freon phase out complete.
Performed heater service. Replaced filter 20x25 and checked operation. System within manufacture specification.
Performed heater service on 1 system. Replaced filters and checked operation. System within manufacture specifications. 16x30,16x25
Performed heater service. Found sysyem operational. Lowered fan speed and removed insulation from restricting blower to outside of cabinet. Replaced filter 20x30.
Performed heater service. System within manufacture specification. Replaced filters and checked for CO.
Performed heater service. Gas was off to furnace. Client said they have never used it. Most likely was left off during visit like this on or ac replacement. I turned it on and checked out. Also opened coil to check for leaks due to ongoing issue. Didnâ€™t find any visible signs of leaks so I made client aware we can sch isolation or we can just â€œsee how it goesâ€ clients are still using ac.
Performed heater service on 1 system. Within manufature spec. Replaced 14x30 filter 16x16 was clean.
Found lines reversed. I switched lines as a courtesy for client.
Performed heater service on 1 system. System within manufacture specifications. 20x25
Performed heater maint. Everything operational within manufature specification. Replaced filters.
Cust ed. On thermostat.