Casey became a service technician at Hyde’s over 6 years ago. He worked in the HVAC business for nearly 16 years and is NATE and EPA certified. When he’s not fixing broken air conditioners, Casey enjoys classic automobile restoration and golfing. Casey advises customers to “be proactive when it comes to your air conditioners and don’t get stuck in the hot summer without it.”
Name: Casey Harrison
Great Follow Up
Dan - Palm Springs, CA
Casey did a great follow up with my paperwork and questions after my installation.
Mike - Palm Desert, CA
Casey did s great job reviewing all the options.
A+ Casey and Hyde’s always give the most professional service !! Fast, friendly and knowledgable!
Sam and Sandi - Palm Desert, CA
Actually look forward to our twice a year “ checkup!” So confident in Hyde’s and Casey!! Client for over 6 years!!!
Glenn - Indio, CA
Great service from Casey
Gary - Indio, CA
Casey was patient; walked us through all of the alternatives; and answered our questions.
Chris - Indian Wells, CA
I had no cold air from my AC and Casey figured out the problem right away. Very professional and very pleasant at a reasonable cost. Thank you.
Great service, good explanation
David - Indio, CA
PAUL - Palm Springs, CA
GREAT EMERGENCY SERVICE. ALWAYS THERE WHEN YOU NEED THEM. 20+ YEARS OF PROFESSIONAL AND HONEST SERVICE.
Response from Hyde's Air Conditioning:
Thank you for recognizing our on call technicians hard work and for your loyalty
Pam - La Quinta, CA
Very patient and courteous
Gloria - Palm Desert, CA
My phone glitches provided ample reason for impatience; however, Casey was very patient and courteous. We appreciate his professionalism.
Added refrigerant to system. Moving condenser Monday.
Performed ac service. Cleared condensation line and condenser coil. System operational but well beyond life expectancy. Client aware of freon phase out and also made her aware of aqmd requirement as of October 1st.
Pulled evaporative coil and chemically cleaned. Installed filter and ptrap on condensationline along with clean out extension. System uses mo99(438a). 30sh 5sc slightly low charge but should cool.
Performed ac service. Cleared condensation line and condenser coil. System 19 yrs old. Operational but beyond life expectancy. Client aware.
Cut out ptrap and flushed line. Must have still been backed up.
Installed 2 water saftey switch. 2 ecobee s and performed ac service. 18x30,20x20,2)14x14.
10 inch damper not completely closing. Order new one warranty.
Found system low on refrigerant. Tenants also complaining about the thermostat. Recommended replacing system client approved replacment of complete system.
Iid check me pass, pass.
Found living room system had a failed contactor. Replaced tested and performed ac service on all 3 system. Removed guest house from the maintenance contract. Not used.
Performed ac service. See report.
Performed ac service on 5 system. Please change the monthly to 5. Cleared condensationmlines and condenser coils. Systems are operational but end of life expectancy. Client aware of age.
Return to check system after thaw. Found system low on refrigerant. Also weak run capacitor. Replaced run capacitor. Client is going to call hw to see what the will do. Most likely leak in evaporative coil.
Performed ac service on 1 system. Found unit operational but weak run capacitor. Recommend replacing run and adding start capacitor. Replaced 45/5 cap and installed starting capacitor. 2)16x20
Found bad cuircut board for bedroom system. Recommend replacing system due to age, refrigerant type and October 1st aqmd requirements. Returned to make sure living system was ok. Newer unit. No issues.
System has major ice build up. Shut system down and Advised to call me to Possibly come out in the am.
Swapped g for common to eliminate batteries when I was here the other day. Found today that 1st stage never worked from the install due to wire nut only connecting two wires in bundle of three.
Common wire from contactor to capacitor overheated and broke connection. Replaced wire.
Performed ac service. System operational. Client want to replace equipment. Freon and furnace emissions issues. sch install for 24th September.
System working properly. Just needs time to cool space down.
Bad compressor. Under warranty. Will order and return to install.