Daniel, son of Michael Hyde, has been an employee of Hyde’s for the last ten years. The Palm Desert native has been involved in the HVAC business since he began working with the company. His NCI and Ygrene certifications help him make valley homes more efficient. Additionally, he enjoys meeting new customers while on the job performing heat load calculations or system maintenance. However, when he’s not working up a sweat outside, one may find him working up a sweat inside the gym.
Testing and Verification Technician
Name: Daniel Hyde
Great service Danny was very good
Mark - Indio, CA
Prompt, Professional, and Friendly
Stephen - Indio, CA
Daniel did a great job getting my AC repaired in a timely fashion. I appreciated how quickly he was able to get to my house after I called. Friendly, polite, and excellent covid precautions. I will use them for all AC service snd repairs going forward.
Jon - Desert Hot Springs, CA
Harry - Rancho Mirage, CA
Thank you, Danny is very professional and very nice
David - Rancho Mirage, CA
Always a pleasure dealing with Hyde’s! Fast response, excellent Technicians. Thanks Danny, great job!
Thomas - Palm Springs, CA
Friendly, gregarious, professional, Took time to explain.
Very professional and friendly
Mark - Palm Springs, CA
Danny did a great job because he was on time, pleasant and friendly, kept me in the loop while he was working, and professional
Danny was thorough, friendly, and solved the problem!
Catherine - Palm Desert, CA
He deserved 5 stars
Preeda - Indio, CA
William - Indian Wells, CA
Still not working correctly. Hope you can return tomorrow.
Upon arrival client stated system set at 77 and reading 83. Found plugged filter. Checked Freon, subcool 8, superheat 18. System is 2002 York r22z Advised on age of system. Advised the issues were dirty filter, age of system and temperature outside.
Upon arrival client stated system not working. Found system running with no issues. Checked capacitors, amps and temperature split. Getting 55 degrees from the supply. Showed client how to check temperature if they think they have a issue. Client showed video of loud condenser noise. Cycled system and no noise occurred. Advised we canâ€™t do anything unless we hear the issue. System is working with no issues.
System had very bad numbers. 575 high 27 superheat 5 subcool 86 suction temp. Removed some Freon I added. 60 degrees from supply, 84 in house. 515 high when left. Advised will follow up Monday. Found condenser fan motor running In low speed, changed to high speed checked amp ok if further problems will need condenser fan motor Paid check . See notes
Upon arrival client stated system blowing warm air. Found dual 50/5 capacitor dead. Replaced and tested. Checked airflow in bedroom. Advised on bar type registers. Signed up on yearly agreement.
Upon arrival found living area contractor bad. Replaced contractor and tested. Units are 1999. Living area 5 ton bedroom 4 ton. Client would like replacement options.
Upon arrival client stated power went out and system not cooking. Found blown high voltage fuse. Replaced and tested. Advised surge protection would have prevent this issue. Office to call and collect.
Upon arrival client stated system blowing warm air. Found capacitor completely dead. Installed capacitor under parts warranty. Signed client up on yearly maintenance agreement. Advised on electrical services. Office to call to schedule maintenance.
Upon arrival client stated bedroom thermostat went blank. Client stated he pulled it off and wall and put it back on and the thermostat turned on. Advised if it happens again to remove Tstat and put back on. Then call Hydeâ€™s and we will replace. Reset filter timer. Advised on sensor and quoted.
Upon arrival client stated system not maintaining temperature. Found system three pounds low on Freon. See picture. Advised on potential leak. Advised on charges but will follow up with the office. Advised 73 trip, 45 per pound.
Upon arrival found system blowing ambient air. Found condenser fan motor bad. Installed new condenser fan motor and capacitor under parts warranty and tested. Client stated card on file was correct but gets declined from user. Office to call and update credit card.
Upon arrival client stated living area blowing ambient air. Found fan capacitor dead. Replaced capacitor and tested. Checked Freon levels. Signed client up on monthly agreement.
Planned parenthood job. Inside office the fau is located inside tbar attic. Found lines clogged and water dripping. Cleared lines. Left message and advised to give the office a call. Advised in issue and charges. Will close out ticket without payment until office gets ahold of authorization. To open ceiling itâ€™s a little hard due to wires blocking.
Upon arrival bedroom system error code 177.03-4. Found system in hard lock out. Checked cda drive and ran test. System passed tests and systems error code went away. Checked Freon. Superheat 40, subcool 7.1. Suction temp 81. Added Freon. Superheat still high at 35, subcool 10.5 and suction temp 73. Advised client possible reasons of what happening. Advised on trip charge. Advised office will call if there is a trip charge.
Upon arrival client stated water by fau. Fau located inside closet. Found lines plugged. Tried to unclog lines, lines took three tries to clear. Lines are cleared. Need to return to install Jones valve. Already collected.
Upon arrival client stated system blowing warm air. Found packaged unit compressor overheated. Checked all capacitors and found all capacitors still within range. Cooled down compressor with a hose. Cycled system and checked Freon levels. Freon levels are perfect see picture. Nothing is over amping. Checked filter and filter is fine. Advised client on compressor overheated but everything checked out okay. Client not happy with new system having issues. Advised if system started to blow ambient air to turn system off and turn fan mode on.
Upon arrival client stated system blowing warm air. Found contractor engaged and 240 volts coming in but nothing going through the contractor. Replaced defective contractor and tested.
Comfort ac service on 2006 carrier five ton packaged unit. Replaced filter, cleared lines and washed coils. Checked all ac components, Freon levels, volts, amps and capacitors. Capacitor rated 80/10 reading 77.6/9.48. Advised on duct modification during the winter time. Signed up on monthly agreement.
Comfort ac service on 2004 carrier packaged unit. Checked lines and replaced filter. Checked temperature split, capacitors and amps. Disconnect box was hard to put back in. Advised client on age of system. Advised anything can happen when itâ€™s past life expectancy. Packaged unit is on roof thatâ€™s hard to get to. See previous debriefing.
Comfort ac service on r410a York split system. Fau located inside hallway attic. Cleared lines on east side of home. Checked all ac components, Freon levels, volts, amps and capacitors. Client had thermostat off and house was 96 degrees. Signed up on yearly agreement.
Upon arrival client stated noise issue. Found no issue upstairs and condenser noise is normal. Advised on no noise issue today. Advised if issue occurs we need to hear it in order to fix it.
Upon arrival client stated system not cooling very well. Freon levels fine, nothingâ€™s over amping. Found both filters plugged. System is 2004 York r22. Advised client on maintenance program. Advised on electrical services. Client interested in maintenance program this winter. Client is part time. Advised on age and type of Freon. Client may be interested in replacement this winter. Also has a hot room.
Comfort ac service on 2018 trane and 2000 York split systems. Fau located inside two attic. Cleared lines by condenser. Wasded coils and replaced filters. Checked all ac components, Freon levels, volts, amps and capacitors. Added 1 pound of Freon on the trane system. Client interested in two next thermostats, run new thermostat wire and move thermostat to other side of the wall. Client interested in duct modification and before and after cfm. Client has two hot bedrooms. See pictures.
Found Freon levels were correct. Client was concerned due to high temperatures this weekend.
Upon arrival client stated blower wouldnâ€™t turn off and thought it was the wcc. Found systems thermostat fan mode on. Turned system off and after 3 minutes the blower turned off. Office to collect I thought credit card was on file.
Comfort ac service on two 2002 York r22 split system. Fau located in garage and casita ceiling. Replaced and washed all filters including ductless system. Cleared condensation lines and washed all condenser coils. Checked all ac components, Freon levels, volts, amps and capacitors. Main house capacitor rated 70/7.5 and reading 71/7.3. Casita capacitor rated 30/5 and reading 29/4. Found casita compressor didnâ€™t turn on. Found casita system low on Freon(see picture). Found suction line 88 degree. Compressor most likely failed due to over heat. Found casita system getting 68 degrees from the supply. Advised client on issue. Client has home warranty. Advised on indoor air quality products. Client stated master bathroom a hot area. Found bathroom register blowing very little air. Advised on duct modification.