Jonathan has been in the HVAC business for seven years and started working for Hyde’s Air Conditioning in the spring of 2013. He grew up in El Centro, CA and graduated from Refrigeration School Inc and is NATE certified. He is constantly learning on the job despite being certified in Electro Magnetic Technologies from RSI. While he may face challenges daily, his favorite part of the job is finding a solution to the problem. In order to minimize the number of air conditioning issues, “Maintain your system to avoid the headaches,” Jonathan said.
Name: Jonathan Ruiz
prompt at a time that we needed service. awesome
Lou perez - Cathedral City, CA
Prompt and great service
Robert - La Quinta, CA
Called prior to arriving, answered all questions and performed all needed service
Jim - Palm Desert, CA
No opinion just wonderful
Earlier than expected. Perfect! Found problems right away!😃
Richard - Palm Desert, CA
Quick and Great as usual thks ankl
Joyce - Palm Desert, CA
Quick to respond and it’s done
Great timely service. Same day service!
Debby - Palm Desert, CA
I love how they send a picture of the technician who is coming to your door.
Late evening emergency fix
Arroyoricky - Indio, CA
Jonathan was exceptional in his work, and approach with us. His professionalism is a great representation of Hyde's!!
Honest, efficient and personable
Nancy - Palm Springs, CA
No extra charges for week-end service, reasonable rates and skilled, certified technicians....you cannot go wrong with Hydes.
Laura - Palm Springs, CA
Jonathon was awesome
Liliane - Indio, CA
Tested equipment and found units capacitor was low, I also tested equipments refrigerant pressures and found high super heat. Added 2 pounds of R-422b all I had and was able to lower superheat to 10. There was only a 17-18 degree split. Advise tenant to run equipment and let it cool off. Also replaced filter in home.
At arrival tested equipment and found leak at condensing unit, I bubble tested and leak was accessible/repairable. Quoted homeowner to repair leak and for approval. Repaired leak, put system in a vacuum and recharged equipment with R-410a refrigerant. Ran system and equipment is running properly at this time. Office to run credit card on file.
Homeowner had to download app to phone. Downloaded Total comfort app then tested, thermostat responded.
Assisted tech with no cool, bad disconnect box.
Tested equipment and found everything running properly. Start up noise us normal.
Maintenance on 3 cooling systems. Tested equipment and found all system pressure and components working properly and within limits. Washed filters, condenser coils and replaced filters in home.
Maintenance on cooling system. Tested equipment and found everything running properly and within limits. Washed condenser coil and clean electrical components.
Master bedroom packaged unit low on refrigerant. Homeowner to contact home warranty.
Found defective high voltage fuse, replaced and tested. Checked electrical equipment and found everything running properly and within limits.
Found burnt wire on load side which burnt through common wire. Common wire fed through and burnt interface module and circuit board. I fixed burnt wire, interface module and circuit board. System is running properly and cooling at this time.
Replaced defective compressor on American Standard equipment. Had to weld in conversion kits for compressor. Charged system with R-410a refrigerant and tested equipment. Unit cooling properly at this time.
Called left voicemail, office called and also left voicemail. Rang door bell stood by 15.
Maintenance on 2 cooling systems. Packaged units on roof, tested equipment and found everything running properly and within limits. Replaced filters and washed condenser coils.
Replaced defective compressor unit 4.
Found defective compressor on a 2 compressor unit for work out area. Units serial number 4514P36580. Need to order compressor.
Conducted maintenance on cooling system. Tested equipment and found system pressures and component readings to be ok and within limits. I washed condenser and replaced filters in home. Cleared condensation line on side of the house. Fixed exposed condenser fan motor wires. Homeowner asked about replacing condensing coils that were bent (cosmetic) advised that it wasnâ€™t necessary since equipment was still working properly. Collected for Hydeâ€™s comfort plan.
Tested equipment and found unit running properly at arrival. Disconnected equipment and when I retested I found contactor was bouncing and not making contact therefore compressor shutting off. I replaced contactor and tested, unit cooling properly at this time. Also replaced filter 14/30.
Maintenance on 2 cooling systems. Tested packaged unit for home and found equipment to be running properly and within limits. Packaged unit is a 2007 Payne unit. Also tested split system, Trane unit 1993 unit. Found defective start kit and a dual run capacitor that was out of range. Replaced both components and tested per homeowner. Found system pressures to be ok and within limits. Washed condenser coils and replaced all filters in home.Once about to collect, homeowner advised she had a home warranty. She then asked me to remove capacitor and hard start kit. I then was about to remove them when she advised to leave them once she called home warranty and they told her they wonâ€™t replace unless broken. Again she told me to remove components since she was ok if one system broke down. I then advice of service call charge.
Tested equipment and found system pressures ok, checked all electrical components again and everything is within limits. Thermostats in living room and near kitchen wonâ€™t drop below 85. Checked airflow, crawled in attic to check dampers manualy. Open a duct and check damper found it to be open but little airflow. Didnâ€™t do any additional test. Need to return and speak to Barry regarding call.
Found compressor for bedrooms system was overheated, pour water on top of compressor for 30 minutes and it wouldnâ€™t reset. Advise client to let system sit for an hour and try to turn it on. Will contact homeowner in one hour.Compressor bad, wonâ€™t reset internal overload.
Tested equipment pressures and found unit low on refrigerant, added 2 pounds of R-22 refrigerant and tested. System pressures are ok this time.
Found pinched wire causing unit to cycle on and off. Moved wire and tested, unit running properly at this time.
At arrival tested equipment and found unit low on refrigerant. Added 4 pounds of R410a and tested, also replaced a plugged filter. Washed condenser coil that was dirty and found unit cooling properly at this time. We will keep track of Freon.
Thermostat not attach to back plate properly.
Maintenance on cooling system. Tested equipment and found everything running properly and within limits. Washed filter, cleared condensation line and washed condenser coil.