Hyde’s promises customer service that exceeds the expectations of Cathedral City CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Cathedral City CA.
for Cathedral City, CA
Our Reviews by City
Stanley - Cathedral City, CA
Very professional service and information about improvements.
Bruce - Cathedral City, CA
Great staff friendly helpful knowledgeable
Mike - Cathedral City, CA
On time, efficient and Taylor is top notch. Thank you Hyde’s!
Toni - Cathedral City, CA
The best service as usual.I have been a customer since 2003.Everyone is helpful and courteous.Barry is the best.
Pat - Cathedral City, CA
Martha - Cathedral City, CA
Hyde’s Air Conditioning took the time to explain the entire process of replacing our AC system. The customer service I received was exceptional and they were there when they said they would start the project. Thank you Hyde’s.
Gary - Cathedral City, CA
Steve did a fine job of servicing my equipment and giving me some advice as how to save money.
Greg - Cathedral City, CA
Excellent maintenance performed by Frank.
Stephen - Cathedral City, CA
Technician was friendly, informative and very capable.
Great service from Greg!
Darlene - Cathedral City, CA
Love Greg. He knows his business, easy to talk to and he listens. Always a pleasure to have him service both houses. Thank you Greg!
Service heat â€”location garageâ€”washable filter Blower motor run capacitor out of specification (10/7.5) replaced
Reinstall gas piping into the gas valve to make up to code
Check heater components working properly
Comfort heater service on two York split systems. Fau located inside garage and inside closet. Replaced filters in Fau. Checked all heater components, static pressure, volts, amps and capacitors. Recommended water safety switches. Advised on electrical services. Advised on gas pipe not up to code. Wants to fix gas valve pipe and make up to code. Also has some electrical needs. Advised on office to call and schedule.
Maintenance on heating system, furnace located in closet. Found everything running properly and within limits, filters still clean. Cleared condensation line, advised on water safety switch; declined.
Performed annual heating maintenance on two York systems located in separate attics.Checked amps, volts , temperature rise and all safety switches. Both systems are operating and heating properly at time of service.
Performed heating service on two heaters. Both of the manufacture specification. Replaced all filters. Client would like us to upgrade her thermostats to include a sensor for living room.
Check heater components working properly x2 pkg on the roof split in the garage
Performed comfort heater service checked electrical wires and connections replaced filter checked burners blower amps and motors
Service heat(2)â€”atticâ€”access laundry room Highly recommend blower motor run capacitor replacement 2x Out of specification snxxx0274=7.5 is 4.9. Snxxx 0248 7.5=4.8 Capacitors are rated at 7.5 lowest value would be 7.05( capacitors are well out of specification) client to advise Washable filters in bad shape removed and installed throw aways
Performed comfort heater service checked electrical wires and connections replaced filter checked burners blower amps and motors replaced filter cleaned drain.
Performed comfort heater service checked burners blower amps and motors replaced filter cleaned drain checked electrical wires and connections
Performed comfort heater service checked electrical wires and connections replaced filter checked burners blower amps and motors cleaned drain.
System in the garage check heater components working properly
See James notes
We will need to return to replace high limit switch and rollout switch. Due to system is Age parts are hard to find for this unit.
Upon arrival found system calling for cool but inducer draft motor and blower motor are running continuously with no heat.With further inspection discovered a faulty limit switch. Bypass limit switch and test system. System heats when limit switch is bypassed.Mod# L1RA072N16B Ser#L1A040212774.We will be installing new limit switch.
I Performed Maintenance on both the Heating Systems. Also replaced two 20x20 Filters. Both the Heating Systems are 2008 models located in the attic. I also flushed both the condensate drains. Everything else checked out operational at the time of service.
Repleced breaker whit a 40 amps it had a45 max minimum 30 ,installed armo fles in refrigerant line and fixed fan motor wire house is for sale
Performed heating in service. Replace 24 x 24 filter. System within manufacture specifications.
performed heat service. Washable filter. System is operational and within manufature specification. Cleared condensation line. System within manufacture specification. Highly recommend surge protection. Remind client in spring.
Replaced a warranty gas valvePerformed a semi annual heating service on a split system Burners checked out OK Igniters checked out OK Gas pressure checked out OK Induction fan motor checked out OK Blower fan motor checked out OK Electrical checked out OK Thermostat checked out OK Made sure condensation lines were clear Replaced the filter located with in FAU
Performed Hydes family comfort service on the heater.
Upon arrival I found the gas valve was not opening and closing verified voltage and voltage was OK we will reschedule once I have an approval from our client to replace defective valve Please see attached estimate
Performed a semi annual heating service on a Split system Burners checked out OK Igniters checked out OK Gas pressure checked out OK Safety switches checked out OK Induction fan motor checked out OK Blower fan motor checked out OK Electrical checked out OK Thermostat checked out OK Made sure condensation line was clear Changed the filter located with in FAU