Hyde’s promises customer service that exceeds the expectations of Cathedral City CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Cathedral City CA.
for Cathedral City, CA
Our Reviews by City
Virginia - Cathedral City, CA
Great Service. Excellent detail to
Krisko - Cathedral City, CA
Excellent customer service
Donald - Cathedral City, CA
Greg is the best. He is friendly and explains things in a way I can understand. He is consistently professional and thorough
Wendy - Cathedral City, CA
Lovely. Young Man.. Very Knowledgeable!
Maureen - Cathedral City, CA
Thor was very knowledgeable and extremely Courteous!
Hyde's Annual Maintenance
Michael - Cathedral City, CA
Just had my winter annual tune-up by technician James from Hyde's. Prompt, courteous and through. Hyde's program gives me piece of mind and ensures my AC/Heating systems are functioning at their optimum.
Consistent, quality service
Terri A. - Cathedral City, CA
Each person and technician I've interacted with at Hyde's has been courteous and helpful. Technicians are meticulous and helpful. One AC tech even directed our attention to a clogged lint vent from our dryer and we immediately cleaned that out! I have confidence in Hyde's services and crew. That is valuable!
Great Semi annual Service
Bill - Cathedral City, CA
Living in the desert I take no chances with my AC/Heating. My semi annual service check was scheduled and Jeff Sproul was assigned. He not only checked all the motors, wiring, safety controls and filters, he even cleaned the unit (micro dust gets into everything!!). He left me with a sense of confidence that my service contract isn’t just perfunctory. Oh yeah he was also early for the appointment!!
Bill - Cathedral City, CA
Chris from Hyde’s AC and Electric was friendly, knowledgeable and solution focused.
Very gooly service as always. Arrived prompt
Roger - Cathedral City, CA
Rooftop, Check heater system working properly replace 24/24 filter
Made a material list for the 120 V Ductless. Please see attached material list in notes. We will come off the existing 120 V outlet located to the right of the roof access
Put in eco bee all new metal on roof new platform cover and whip sealed all new metal
Found no flashing on roof curb and unlined kd pipe, quote to remove package unit and lift with crane and install 76 x 52 flashing. Remove and metal ducting and fabricate new metal ductwork and plenums . Coordinate with with roofer/HOA. Install Ecobee thermostat
I checked out the system on the roof and I found that everything checked out ok. Then I did a hard reset on the thermostat and tested
Replace damaged duct- Drywall has already been opened by Angelo. Will also install damper in living room supply if possible. Barry Qt around $500. Installers to verify price and they get time and materials.
Quoted on Ductless
I changed out the batteries and tested
Upon arrival I found the circuit breakers to be very old and brittle. There were several circuit breakers that were in the on position but weâ€™re tripped. Replaced circuit breakers tested and all is working per manufacture specifications. There were wires double up on the circuit breakers and that is a against code. Retort tightened all connections within panel. Panel meet local and national code. Tested convenience outlets through office and all are working. Tried to call the client to go over the Hydes family comfort plan and service the air conditioner for approval. Please contact the office to schedule.
14â€ flex 14â€ elbow and start collar
Performed furnace maintenance on 2018 American Standard upflow located within inside closet. Changed 14x25 filter and checked condensate pump to be working properly. Monitored all heating components and all were working properly. Checked capacitors, amps, volts, heat rise and all were to specifications.
Check both FUA in the garage both capacitor are very low one is rated to 15 running at 11.1 the other one is rated to 7.5 running at 6.9 recommended replacement decline at this time Replace 16/25 14/25 filters
I found that the circuit board is malfunctioning and I recommend replacing the circuit board
Attic system is heating properly strongly recommend comfort plan H/O not in home sent email
Added remote sensor to 1050 thermostat under warranty
Mike spoke with customer over phone. Will schedule tech out to diagnose system.
Customer to have Angelo remove bathroom ceiling so we can repair colasped duct 500.00
Perform maintenance on 2017 American standard heat pump. Changed 14x24 filter located underneath furnace platform. Furnace is located in hallway closet. Followed sequence of operation tested capacitor, volts, Amps and reversing valve. Rinsed off condenser coil. Cleared condensation line at furnace. Tested thermostat. Equipment checked out operational at this time.
Replace 1050 under warranty
Removed old condensate hose and cleared pan and made sure water was draining to dirt below
Comfort heater service on 1983 fau and 1985 condenser. Replaced filter
Thermostat keeps rebooting it self we will replace thermostat under warranty 1050
Pkg on the roof check heater components working properly replace 20/20 filter
Service heating furnace located in the garage washable filter at furnace system is heating per manufacture specification