Hyde’s promises customer service that exceeds the expectations of Cathedral City CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Cathedral City CA.
for Cathedral City, CA
Our Reviews by City
Very good service
Kenneth - Cathedral City, CA
As always your technician is professional, prompt and a really nice guy.
Stephen - Cathedral City, CA
Service very professional
Tracey - Cathedral City, CA
Jeff was a super nice man and very very knowledgeable. I would have him as my technician every time Hydes comes out to service my A/C!
Toni - Cathedral City, CA
Excellent as always.Courteous service on the phone.I completely trust Hydes.They have serviced my air conditioning and heating since 2003.
Hyde Is The Best
Charles - Cathedral City, CA
The repairman Greg was wonderful--He knew what he was doing and his knowledge of our equipment was outstanding
The team came out to look at there unit. My Dad was home and met with them he said that the technections came out were very friendly
Heinz - Cathedral City, CA
Thank you again for choosing my parents to win a A/C unit. I called them as soon as I got off the phone with you and told the two of them that they were chosen to win the A/C. The two of them were super happy as I was too. I want to thank you so much, it means a lot to them because they needed one but couldn't afford it. When your team came to there house to look at there unit before they were even chosen I said to them I hope you both win it and my Mom said she would want the person to win it that really needed it. My parents are so kind like that. Thank you again. Birgit
Dependable, Prompt, Expert Service
Mike - Cathedral City, CA
We had our A/C scheduled service today with Danny and were very pleased by the professional demeanor and clear explanation given. Our A/C unit is still running well after installation 4 years ago, and confident with the scheduled maintenance will run many more.
Semi annual AC check
Bill - Cathedral City, CA
On time. Efficient. Good advice.
Great service by Steve Martin— he went the extra mile.
Gerald - Cathedral City, CA
Steve gave us quality information on our AC.
The young men were very personable and knowledgeable. A true asset to your Company...
Maureen - Cathedral City, CA
Cooling components working properly
I installed the hard start kit and tested. On start up it was pulling (83) amps
Basic maintenance, change notes to washable dilter, good pressures
Regulat maintenance, pressures good, coil cleaned, condensate cleared outside underground
I performed a maintenance on (1) cooling system and I found that everything checked out ok. Then I changed out (1) filters located on the ground
Performed ac service on two systems. Both within man. Spec.
Client to reschedule
Check system cooling components working properly
Cooling components working properly
Performed annual AC maintenance on Kenmore package unit. Changed 14 x 20 x 1 filter. Checked amps, volts, capacitor and all other electrical components. Checked refrigerant levels, superheat, sub cool and temperature split.Flushed condensation line and washed condensing coil. Found all electrical components and refrigerant levels to be within manufacture specifications. System is operating and cooling properly at time of service.
Call = unit wonâ€™t turn offâ€”-(I called client and had them pull disconnect))Sn 10093 stuck contactor â€” replace contactor on both condensers NOTE: had made recommendations to replace contactor(2x) on last visit â€”yesterday
Check cooling system found fan motor out range replace capacitor system working properly
Service air-conditioning package unit located on the roof filter is a 24 x 24 located in the hallway run capacitor start capacitor and refrigerant levels are within specification running and starting amps in specification
Installed a 2.5 ton upflow system with condensate pump.
Service cooling furnace is located in the garage condensers backyard â€”-Serial# 10093 ( high head pressure) system has a restriction also compressor starting over rated amps replaced faulty start kits Sn 2026 refrigerant within specification Both units need contactor replaced ( very pitted)â€” client to call if wants work
Performed Hydeâ€™s comfort summer service added a 1/2 pound r22 amps cap good clear drain washed
Performed a semi annual cooling service on a split system Refrigerant checked out OK Electrical checked out OK Compressor checked out OK Condensing fan motor checked out OK Contactor checked out OK Capacitor checked out OK Thermostat checked out OK Cleared condensation lines with CO2 Rinsed condensing unit out with H2O Changed the filters located within the Dwelling
Found system low on refrigerant. Added 2 lbs to help client stay cool until decision is made.
Installed Honeywell 5000 thermostat and explained operation
Comfort ac service on platinum American standard split system. Fau located inside attic. Cleared lines, washed coils and client had already replaced filters. Checked all ac complete and freon levels.
Performed a semi annual cooling service on two split system Refrigerant checked out OK Electrical checked out OK Compressor checked out OK Condensing fan motor checked out OK Contactor checked out OK Capacitor checked out OK Thermostat checked out OK Cleared condensation lines with CO2 Rinsed condensing unit out with H2O Supplied the filters to our client
Ac service.cleared condenser coils and condensation line. System within man. Spec. Uv dated 2016 if you want the bulb changed let us know for next visit.
Check out job. 2.5 ton upflow with condensate pump.
Performed comfort cooling services checked electrical wires and connections replaced filter cleaned drain checked Freon levels amps and motors.