Hyde’s promises customer service that exceeds the expectations of Cathedral City CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Cathedral City CA.
for Cathedral City, CA
Our Reviews by City
Tim is the best service tech
Norman - Cathedral City, CA
Ray - Cathedral City, CA
Very thorough , neat and professional
Great customer service
Caroline - Cathedral City, CA
Caroline - Cathedral City, CA
Cindy - Cathedral City, CA
Prompt and great service
Al - Cathedral City, CA
Technician was excellent and carefully explained what was happening and the correction he suggested we take. Not only was he polite, he was thorough and made sure everything that needed to be done was done to our satisfaction.
Debbie - Cathedral City, CA
$194 for a capacitor really? Good to know I'll never use you again plus teach Greg how to drive and maybe slow down so he doesn't miss the house to begin with and then need to back up on a busy busy street and then end up hitting my mailboxes
James - Cathedral City, CA
Spring tune-up (twice a year for 9 years)
Brian - Cathedral City, CA
James was excellent at his job! Reinstalled a thermostat that had taken apart and couldn't get to work along with his other duties
Always great service
Randy - Cathedral City, CA
I performed a maintenance on (3) cooling systems and I found that everything checked out ok. Then I changed out (3) filters located on the ground
Service coolâ€” attic and ground Condenser back yard must carry tools thru home
Order coil under warranty from goodman we will be installing evaporate coil Monday 4/22/19
Find arrival found system off so I turn system on to cool from thermostat but condensing unit would not operate. With further inspection and the help of Jeff we discovered a broken wire underneath the mobile home. Change the wire and test system. System is now operational
I performed a maintenance on (2) cooling systems and I found that the system serving the east side of house was (1) pounds low on R-410a freon and I recharge the system and tested. Then I changed out (2) filters located on the ground . I also adjusted the register and advise client about putting damper in to adjust airflow.
Finish install of registers
Found 3.5 heat pump up flow in poor shape and low Freon. We will need a extra long shot crane for this install .unable to reach owner, left message on voice mail.
Performed comfort cooling service
Install 2â€“ one way curved blade register
Comfort ac service on 2013 Trans split system. Fau located inside closet. Replaced filters and washed coils. Checked all ac componets, freon levels, volts, amps and capacitors. Found fan motor capacitor outside its range. Replaced capacitor and tested unit. Signed up on yearly agreement.
Need to return tomorrow morning
Myself and the office both called a client with no answer or call back. Standby for 20 minutes but had to move on.
Dropped warranty book off, went over system and installed hand held remote for upstairs bedroom. Will mail check for $215 to customer for maintenance.
Installed 460 volt 3 phase condenser fan motors one on HP 1 and HP 2
Finance Office not cooling HP4 found bad blower contactor. Replaced contactor . HP1 and HP 2 need condenser fan motors will order
Faulty dual run capacitor 45/5â€“replaced and test ==ok Fan amps tested =ok Refrigerant Target 9 â€”-is 2 ( unit low on refrigerant ) Low voltage wire damaged at condenser Recommend service planâ€” wire repair â€”refrigerant add Client not interested in service plan or repair
Install team will connect unit
Measure house and load calc.
Performed a semiannual cooling service on a split system Refrigerant checked out OK Electrical checked out OK Contactor checked out OK Compressor checked out OK Condensing fan motor checked out OK Thermostat checked out OK Cleared condensate line with CO2 Rinsed condensing unit out with H2O Changed the filter located with in the dwellingUpon arrival the Nexia thermostat was not connected to the Internet. Connected to the Internet and our clients cell phone. Tested and all is working per manufacturers specifications
I removed the existing return filter grill located in the laundry room and I installed the new filter return grill
Upon arrival system wasnâ€™t working checked wire were defective fron furnace to thermostat replaced wires then contactor 24 v coil was demand replaced contactor system working properly
I Performed Maintenance on both of the Cooling Systems. Also replaced a 20x20 16x16 and 12x12 Filters. Both Cooling Systems are 3 Ton models located on the ground. I also flushed the condensate drains. I found that both of the systems are Icing up due to low Airflow. I advised client that with the age of the system and R-22 being phased out next year, I would strongly recommend replacing both systems. Client would like to have Barry come out and go over options with them. Client will call in to schedule appointment.
Performed annual AC maintenance on to York split systems and one good been rooftop package unit. Changed 20 x 20 by one, 20 x 25 x 1 and 14 x 24 x 1 filters. Checked amps, vote, temperature split and all electrical components. Checked refrigerant levels, superheat, and sub cool and lying temperatures. All three systems are operating and cooling properly at time of service.
Performed a semiannual cooling service on a package unit Refrigerant Was Low on R22 Electrical checked out OK Contactor checked out OK Capacitor checked out OK Compressor checked out OK Condensing fan motor checked out OK Thermostat checked out OK Cleared condensate line with CO2 Rinsed condensing unit out with H2O Changed the filter located with in the dwelling
Comfort ac service on new American standard split system. Fau located inside hallway attic. Replaced filter, washed coils and cleared lines on north side of home. Checked all ac components and freon levels.