Hyde’s promises customer service that exceeds the expectations of Indian Wells CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Indian Wells CA.
for Indian Wells, CA
Our Reviews by City
Very good service
Rodger - Indian Wells, CA
Sandra - Indian Wells, CA
Harold - Indian Wells, CA
Always superior service!
Alfredo - Indian Wells, CA
Always on time and with an accurate and fair quote.
Great service. Trustworthy. High integrity.
David - Indian Wells, CA
Always great service!!!
Mark - Indian Wells, CA
Always Superior Service
Carolyn - Indian Wells, CA
The only company to hire in Coachella Valley for heating & cooling!
Casey did great job as usual.
Norman - Indian Wells, CA
Professional and thorough.
Walt - Indian Wells, CA
Steve - Indian Wells, CA
Estimate. Advised she needs 2 smoke and 2 CO detectors
Comfort heater service on three split systems. Fau located inside golf cart garage and southeast side of homes outside closet. Replaced all filters. Checked all heater components, static pressure, volts and amps. Advised on gas pipe not being up to code. Advised on electrical services.
Performed heating service on one system. 24 x 24 filter 14 x 24 filter. System operational and within manufacture specification. made Client aware of system age over 10.
Performed heating service on three systems. All systems within manufacture specification. Living room system had a pressure switch issue that I resolved by tapping on pressure switch. Made Kline aware of the issue if it happens again we will need to replace the pressure switch this is the living room system. Replaced all filters
Comfort heater service on two American standard split systems. Fau located inside garage and north side of home outside closet. Checked all heater components, static pressure, volts and amps. Washed eac filters. Cleaned both Fau from any dust, bugs and spider webs.
Clean blower wheel and housing3.5-4 hr job Job completed â€” test both systems after cleaning=ok Jumper blowers = Use card xxxxxxx7023 ( always have problems withâ€project )
I removed (2) thermostat and installed (2) client supplied Nest thermostat and tested
Performed annual heater maintenance on two rooftop package unit. Changed two 24 x 24 x 1 filters. Checked amps, volts, temperature rise and all safety switches. Checked in gas and static pressures. Both systems are operating the heating properly at time of service.
Performed annual heater maintenance on two 2018 American standard split systems. Both systems are located inside garage closet. Washed washable filters. Checked amps, volts, temperature rise and all safety switches. Checked gas and static pressures. Flush both condensation lines. Both systems are operating and heating properly at time of service.
Maintenance on 3 heating systems. Tested and found everything running properly and within limits, washable filters. Cleared condensation lines.
Removed 8 feet from the 12 inch run and then I had a significant air to daughters room
Replaced warrantee louver motor
I returned and I replaced the UV bulb to the kitchen system and installed the fourth uv light to the guest bedroom system and tested
I performed a maintenance on (2) heating systems and I found that everything checked out ok. Then I cleaned out (2) filters and flushed out the condensate drains located on the ground (1)2014 (1)2015 models
Service heat (2)â€”location outside closetâ€” filter washable Recommend blower wheel and housing cleanâ€” client to follow up â€”see estimate
Client thought condenser had moved. It had not moved they just cleared the brush and now you can see it a little better and itâ€™s a pad sitting on a pad. I told him not to mess with it because it makes room for us to stand when working on it. I updated there are 950s to the newest software
Service heat (2) roof packageâ€”filter 14/36â€“24/24 Recommend sn xxx966L 1) Pull and clean blower wheel and housing 2) insrinstall. UV liteâ€”see estimate
Performed heater service on 5 systems. Found all systems within manufature spec. Need to bring all the filters next visit.
Comfort heater service on two 2005 American standard split systems. Fau located inside garage closet and outside closet. Checked all heater components and washed filters.
Service heatâ€”atticâ€” access hallway Client concerned not enough air daughter roomâ€” Greg to follow up with mike/ Barryâ€”-(+30â€™ see photo)
Performed a semi annual heating service on two split systems Burners checked out OK Igniters checked out OK Gas pressure checked out OK Carbon monoxide levels checked out OK Electrical checked out OK Safety switches checked out OK Induction fan motor checked out OK Blower fan motor checked out OK Made sure condensation lines were clear Changed the filters located with in the FAU
Service heat(5) Attic MB closet (2) Attic kitchen hallway (2) need 22 foot extension ladder to get into attic â€” floor is wood use cautionâ€” ( I tapped feet of ladder to protect floor Garage closet (1) OFFICE PLS NOTE 22FOOT extension Ladder need to reach attic
Found a nest thermostat wired incorrectly as well as equipment settings wrong. Fixed problem and sign Kline up on comfort service call To schedule. 2)20x30
Performed service on five systems. All heaters are within manufacture specifications. Found the living room and great room systems have history of leaks one slightly low today. All the systems are beyond life expectancy. And all carry Freon which is been phased out since 2010. By 2020 theyâ€™re going to stop production of Freon. I also wrapped most of the line sets with the UV per code I have to return to finish the last two units. I can talk to the client a little bit about the condition when I do this.
I performed a maintenance on (3) heating systems and I found that everything checked out ok. Then I changed out (5) filters and flushed out the condensate drains (2) located in the attic (1) located on the ground (3)2014 models