Hyde’s promises customer service that exceeds the expectations of Indian Wells CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Indian Wells CA.
for Indian Wells, CA
Our Reviews by City
Sandi - Indian Wells, CA
Timely service, well done
Peter - Indian Wells, CA
James was a treat to work with.
First class service from Casey as usual !!
Norman - Indian Wells, CA
Prompt &Knowledgeable Service
Cindy - Indian Wells, CA
Hyde’s was out within a few hours of contacting them with our problems. I received notification when the technician was on his way. He was very thorough. Explained everything as he was working. And had our problem corrected in a timely fashion. Cost seemed fair.
Bob - Indian Wells, CA
Greg was awesome
John - Indian Wells, CA
David - Indian Wells, CA
An Absolute Professional
Conn - Indian Wells, CA
The Hydes technicians are amazing. On time, helpful, explain anything that I ask about, and do a great job. I’ve been thoroughly pleased with every aspect of their service.
Definitely skilled workers
Paul - Indian Wells, CA
Just started with Hyde’s this year. Terrific service and very professional and friendly technicians. I would definitely recommend them.
Beverly - Indian Wells, CA
Estimate for bedroom unit.
Comfort heater service on 2010 Amana split system. Fau located inside the garage. Cleared condensation line. Found a lot of water in the line. Checked all heater components, static pressure, volts and amps. Replaced filter. Advised on electrical services.
Installed a 5 Ton Platinum 20 Upflow Split Heat Pump.
Stopped to check job out and go over few things with installers.
Homeowner Lisa turner - 206-499-2854 Lturnerpm@me.com Have a manager come out to give estimate on new system And ducting upgrades General contractor Jose Garcia email@example.com 760.619.4458
Did not perform heater service. Upon arrival I advised client I am here to do a heate service. Client was upset because she said duct pros were here this morning and I was supposed to be here. Advised on being here during my scheduled time frame. Checked bedroom unit and found covers and filters removed. Advised client if I do one heater maintenance we would have to return to do the other fau. Removed coil cover and exhaust to give duct pros visual access to supply duct. See picture. Sent duct pros a picture. Return and reinstalled coil and all panels.
Performed heater service on 3 systems. Both main home systems were cycling high limit. Increased fan speed and I believe I have solved the problem. I made client aware incase she had a warranty for the home. New home in toscana. Replaced all filters and signed on hfcp. Sch. Maint for late April
Performed annual heater maintenance on two 2007 American standard rooftop package units. Wash washable filters. Checked amps, volts, temperature rise and all safety switches. Checked gas and static pressures also flush condensation lines. Found all electrical and safety components to be within manufacture specifications. Both systems are operating and heating properly at time of service.
Heat service on all 5 systems. Filters good until Next visit. All systems operational and within manufacture specification.
Comfort heater service on three 1998 York r22 split systems. Fau located inside garage and outside closet. Thermostats in hallway, downstairs and master bedroom. Replaced all filters. Checked all heater components, static pressure, volts, amps and capacitors. Found downstairs 2 ton system plug at fau had loose connection. Replaced batteries in downstairs unit. Found living area system in garage had capacitor outside itâ€™s range, replaced and tested. Signed up on yearly agreement. Mike to follow up with estimate, living area 5 ton, downstairs 2 ton and master could not read plate. Advised on age and type of Freon. Advised on December special. Systems are well past life expectancy.
Upon arrival found living area packaged unit running in cooling mode. Client was concerned about a noise. Advised client system is constantly running and found compressor iced up. Found common wire touching somewhere from the thermostat and the packaged unit. Wire created a short and blew the transformer. Installed focus 6000 thermostat. Replaced transformer. Removed common wire and added batteries to the thermostat. Educated client on thermostat and set the schedule. Verified split of the home with each system.
Checked all rollout switch and high limit switches. Cycled system at circuitboard and thermostat system now operating properly.
Upon arrival found system calling for heat and blower motor operating continuously. With further inspection I discovered system had a trip to roll out switch. Reset rollout switch and monitored system. System is now heating properly.
Service Heating two times furnaces are located outside closet â€”-outside closet is located in backyard both furnaces Heating per manufacture specification replaced both blower motor run capacitorâ€˜s serial number 9537 out of specification serial number 4619 replaced due to age Filters areide louvered closet
Check both heater inside garage both heater working properly recommended replacement customer will call after holiday to replace system
Inside closet check heater system wash filter clean condensation line heater working properly
Found igniter wire off at circuitboard reattached igniter wire unit working per manufacture specification wire was probably knocked off at last call no charge
Phone quote on air schubbers
Estimate for guest bedrooms on east side of house.
Service heating furnace is located inside closetâ€”- closet is located in the hallway â€”-filters are 14/24 in 20/30 â€”/blower motor run capacitor out of specification recommend replacementâ€”â€” recommend cleaning of blower motor blower wheel and housing dirty with construction dust â€” client wanted nothing done at this timeâ€” sent estimate â€”- temp rise good clear condensate from unit
1)Serial number 1613 package unit on the roof replaced repaired low-voltage wiring at roof 2)Serial number X X X located backyard outside closet run hard gas pipe through cabinet( bring up to code) and install new thermostat 5000
I Performed Maintenance on both of the Heating Systems. Also cleaned both washable filters. Both Heating Systems are 2014 models located in the outside closets. I also flushed both of the condensate drains. Everything else checked out operational at the time of service.
I will need to order a lamp for the ceiling fan. I will call Client when the lamp comes in. Replaced the halogen lamp in her ceiling fan. Purchased an extra one as itâ€™s a special order lamp
Installed 8000 stat and gate way
I Performed Maintenance on both of the Heating Systems. Also replaced a 20x30 and 4) 20x20 Filters. Both Heating Systems are 2009 models located in the garage and in the outside closet. I also flushed both of the condensate drains. Everything else checked out operational at the time of service.