Hyde’s promises customer service that exceeds the expectations of Indian Wells CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Indian Wells CA.
for Indian Wells, CA
Our Reviews by City
FIFTY STAR SERVICE
Isabel - Indian Wells, CA
Efficient service - 👍
Sandee - Indian Wells, CA
Courteous, timely and effiicient.
Patrick - Indian Wells, CA
Casey is a hard working and efficient mechanic. He has worked with us before and represents his company professionally.
Great service. Very thorough. Starbucks card a nice touch. No issues good new.
Pat - Indian Wells, CA
Nancy - Indian Wells, CA
Carolyn - Indian Wells, CA
Austin - Indian Wells, CA
Emmett - Indian Wells, CA
Knowledgeable and professional
Jean - Indian Wells, CA
Service Technician Casey arrived on time and was professional, knowledgeable and friendly. Casey provided us with suggestions as to how we can modify our current HVAC system to maximize its effectiveness and longevity. Once again we are happy customers. Thanks Hyde’s!
The usual great service & promptness
Diana - Indian Wells, CA
The review header says it all. Very nice & informed man
Performed comfort heater services checked burners blower amps and motors replaced filters checked thermostats . Checked electrical wires and connections. Cleaned drain cleaned. Sold 2 -50gal water heaters.
Performed 4 system heating service. All systems are operational. Replace all filters. Recommend surge protection.
Furnace working intermittentlyâ€”sn xxx1631( had tried pin connector adjust â€” worked than didnâ€™t) replaced circuit board and test system working as designed
Maintenance on 2 heating systems, tested and found everything running properly and within limits. Replaced filters and cleared condensation lines.
Comfort heater service on three 2004 Bryant split systems. Fau located in master closet attic(2), garage and casita garage. Replaced filters throughout the house and casita. Checked all heater components, static pressure, volts, amps and capacitors. Advised on age of units and life expectancy. Mike to follow up with air flow testing estimate.
Performed annual heater maintenance on two American standard split systems. Systems are located on the ground and outside closet. Washed washable filters. Checked amps, volts, temperature rise and all safety switches. Checked gas and static pressures also flushed condensation line. Recommend installing condensation water safety switch to prevent any water damage to the home or equipment due to condensation leak or overflow.
Unit running upon arrival â€”- intermittent issue Will order circuit board Amana
Performed heat service. Signed client up on family comfort plan. Both systems operational. Systems installed by us in 2015. Systems within man spec. schduled next visit in field. May 7th
Performed comfort heater services checked burners blower amps and motors replaced filters clean drains checked electrical wires and connections replaced filters. All heater operation test normal and safe.
Client had canceled when I got to the house.
. Performed comfort heater service checked burners blower amps and motors replaced filter cleaned drain checked electrical wires and connections.
Furnace Snxxx1631 heater working intermittentlyâ€” found pin connector not secured ( see photo)â€” removed pin connector check adjusted wiringâ€”reinstall and testâ€” furnace working properlyâ€” inform client of possible condensation issue in attic Talked at length about service plan â€”client not at this time
Master bedroom system not heating upon arrival I found just the inducer running. The sight glass is in a bad spot and I couldnâ€™t see the diagnostic lights. After a reset the system came on and cycled normally. Made client aware it may is intermittent and to call if it happens again and see if we can catch it in the act. Client mentioned age and replacement I told her they are at the end of life expectancy. May want to consider replacement.
Performed comfort heater service checked burners blower amps and motors replaced filter cleaned drain checked electrical wires and connections
Upon arrival I found the mini split that services air to the storage room was completely dirty.Performed a service on both mini splits. 1. Server Room 2. Storage RoomBoth systems are working per manufacturers specifications
Provided an estimate for electrical work
Performed heater service on two systems. Client has us come out 4 times a year. Client had to go please call to collect for renewal.
Service heat(2x)â€”location roof Discussed age of systems â€” tech to follow up mid February (see photos and notes) CO tested on both systems none detected Replaced tstat(5000) live system
Found bad thermostat turning the ac on instead of heat. Was working day ago and I did check the programming of the thermostat just to be safe and it was programmed properly. I istalled ecobee 3.
Quoted on a Daikin Ductless
Comfort heater service on 2014 American standard split system. Fau located inside closet. Replaced filter in Fau. Checked all heater components, static pressure, volts, amps and temperature split. Reset filter timer on thermostat. Filled out Fau inspection form.
I performed a maintenance on (2) heating systems and I found that both systems are in poor condition and needs to be replaced and I advise client about the systems. Then I changed out (2) filters and flushed out the condensate drain located on the roof
Performed heat service on 3 systems. Found all systems are operational. The master bedroom system is showing signs of ware. System is beyond life expectancy. Recommended system replacement for master.also recommended surge protection.
I performed a maintenance on (2) heating systems and I found that everything checked out ok. Then I changed out (2) filters and flushed out the condensate drains located on the roof
Service heatâ€”garage and outside closet