Hyde’s promises customer service that exceeds the expectations of Indian Wells CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Indian Wells CA.
for Indian Wells, CA
Our Reviews by City
Prompt service, he took care of our problems
Jack - Indian Wells, CA
Diana - Indian Wells, CA
Frank has performed service at my home before and he is great. He went above & beyond today helping me replace my smoke detector batteries. Thank you
great service,awesome price
Siu - Indian Wells, CA
The technician is pleasant,helpful. I highly recommend him to any one who needs services.
Helpful. Polite. On time
Linda - Indian Wells, CA
George - Indian Wells, CA
Thor did an excellent job servicing all our heating and air conditioning units
Response from Hyde's Air Conditioning:
Mary - Indian Wells, CA
Great personable service
Mike - Indian Wells, CA
Casey was on time, knowledgeable and efficient. Always is.
Ed - Indian Wells, CA
Danny arrived early in the appointment window, which is always appreciated. He explained exactly what he would be doing, and completed the multiple system checks with a minimum of disruption to the household (and put up with the barking dogs very patiently). He mentioned a note he added to our file to have the condensate line cleared during each service visit, and explained the current offers for a new water heater with the purchase of a new a/c unit and advised us of their abilities with the new electrical services. He advised that our current system, while now 9 or so years old, was functioning within specifications. Danny was very pleasant and professional during his service call.
Sandi - Indian Wells, CA
Timely service, well done
Peter - Indian Wells, CA
James was a treat to work with.
Inside closet check both heater system clean condensation line wash both filter system working properly
Rooftop, service two pkg system checked heater components working properly replace 24/24 20/30 filter
Replace ECM motor for living room system tested working properly advice system are in need of service recommend HYDES comfort planN
Service Heating two times â€”â€” furnace located outside closet by front door â€”â€”filters with furnaceâ€”-@@ both furnaces are heating per manufacturers specificationsâ€”â€” Serial number 5563 left-hand side of closet broken float switch and â€œactive Techâ€ UV light not workingâ€”-Recommend replacing both UV lights and replace broken water switch â€” Also recommend Serial Iâ€™lllol number 5560 move or replace existing water switch into secondary evaporate lcoil drain outlet-see photos for model and serial numbers also UV light informationâ€”Estimate sent for water switch work (2x)and replacing UV lights (2x)
Recommend hard pipe to furnace cabinet reference bring up to building code 01-16-20 Return install hard pipe through furnace cabinet with drip leg
I Performed Maintenance on both of the Heating Systems. Also cleaned both washable filters and flushed both the condensate drains. Both Heating Systems are 2018 models located in the garage. Everything else checked out operational at the time of service.
Replace with new transformer and checked all lights to be working
We will be installing a new transformer tomorrow. Electrical distributor is closed.
I removed the existing inducer fan motor and then I installed the new inducer fan motor and tested
Upon arrival living room system wasnâ€™t working after further inspection found BAD ECM BLOWER MOTOR check #5227
Master bedroom thermostat is a 1050 will not connect to Wi-Fi other thermostats in his home are connecting to Wi-Fi â€”-Tech to follow up with new 1050 office will call and schedule service on thermostat â€”â€”warrantee call new 1050 was Installed May 20
Attic check heater system working properly clean condensation line replace filters
Performed furnace maintenance on (2) 2013 American Standard upflow systems located in garage and outside closet. Cleared out both condensate drains and cleaned both washable filters. Checked amps, volts, capacitors and all were good. Checked heat rise and static pressures and both were within nameplate ranges. Monitored all heating components and all were working properly. Checked both safety switches and both were working. Customer paid by check.
I found that the inducer fan motor winding was broken at the connection and I wired the winding to direct power to temporarily to get the inducer fan motor working until we can get the new inducer fan motor on Monday to replace
No heat. Tstat blank. Found furnace flashing 33 lock out. Low voltage 12. Good fuse pressed all Manuel reset safetyâ€™s and furnace fired. Cycled and monitored no concerns. Possible issue from prior surge client said he had.
Duct pro found supply filled with dirt options are too run in attic will need to pull furnace out for access
Performed furnace maintenance on two 2012 American Standard upflow units ( located in inside and outside closets). Changed 24x24 filter with indoor fau and 20x25 located with outdoor fau. Cleared both condensate drains. Monitored all heating and electrical components and all were operating to specifications.
Client complaint of cold air blowing on them. Ran heater and system started and heat works. Client mentioned he did see the fan on and turned it off. I assume the fan got turned on and was running continuesly.
Preformed a semi annual heating service on 2013 American standard split system Changed 20x25 filter located at furnace/ furnace is located in inside closet Followed sequence of operation tested thermostat, volts, amps, heating safety switch and temperature rise. Cleared out condensation drain line. Cleaned out burners, electrical and furnace. Equipment checked out operational at this visit.
Performed a semi annual heating service on two 2017 American standard split system. Changed two 20x25 filters located at furnace. Furnace is located in garage. Followed sequence of operation tested inducer fan motor, heating safety switch, volts and amps. Cleared out condensation drain line. Cleaned out burners, electrical and furnace. Cleaned return register in ceiling. Both thermostat checked thermostat ok Equipment checked out operational at this visit Homeowner will call office to renew contract
I found that the batteries were no good and I replaced the batteries client supplied
Performed furnace maintenance on two package units on roof. Cleared out both condensate lines. Changed 24x24 and 14x36 filters. Checked capacitors, volts, amps, heat rise, and all checked out to specifications.
Service Heating two times â€” furnace is located in the attic two separate attic accesses media filter at one furnace and EAC at the other furnace â€”/recommend 2 water switches at safety pans additional condensate drain line work needed see photo â€”-client OK with running primary drain line out of attic and down side of house that would be for the bedroom unit see estimate Condensate primary drain lines are interconnected also have safety pan connected as well with primary â€”- see estimate and photos
Replace BBQ light
2006 2004 water heater. Mike on Monday. Old ducts, no garage insulation. Sold cap