Hyde’s promises customer service that exceeds the expectations of Indian Wells CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Indian Wells CA.
for Indian Wells, CA
Our Reviews by City
Joel - Indian Wells, CA
Johnny was excellent!
Joel - Indian Wells, CA
Good explanations& friendly
Rodger - Indian Wells, CA
James - Indian Wells, CA
Casey always does a great job. He is a pleasure to work with and very informative. However Juan in your office is terrible. He is rude, Condescending , sarcastic, and insufferable to deal with
Mary - Indian Wells, CA
Diana - Indian Wells, CA
Fast, efficient, informative
David - Indian Wells, CA
Mary - Indian Wells, CA
Cris was very knowledgeable and coda superb job!
Informative, polite - great service
Harold - Indian Wells, CA
Semi annual service
Eugene - Indian Wells, CA
As usual Hyde's did it again with great service and professional staff, All work was expertly done while we were away. Staff called us and explained all the work and the reasons for it. Fair price and discounted since we have the annual maintenance agreement.
Service Cooling two times location of condenser left-hand side of home refrigerant numbers both units within specification serial number 5646 replace still run capacitor due to age
Install three ceiling fans for customer check all fans and all fans checked good
Comfort ac service on 2015 American standard split system. Replaced filter, cleared lines and washed coils. Checked all ac component, freon levels, volts, amps, capacitors and temperature split. Added hard start kit to increase the life of the compressor. Signed up on yearly agreement.
Performed a semi annual cooling service on two package units Refrigerant checked out OK Electrical checked out OK Compressor checked out OK Condensing fan motor checked out OK Contactor checked out OK Capacitor checked out OK Thermostat checked out OK Cleared condensation lines with CO2 Rinsed condensing unit out with H2O Changed the filters located within the Dwelling
Looks like the shrader was leaking. Pressurized @400 psi 10min held. Recharged system.
Performed a semi annual cooling service on two package unit Refrigerant checked out OK Electrical checked out OK Compressor checked out OK Condensing fan motor checked out OK Contactor checked out OK Capacitor checked out OK Thermostat checked out OK Cleared condensation lines with CO2 Rinsed condensing unit out with H2O Changed the filters located within the Dwelling
Paid in full as follows Isolation test Temp repair New line-sets
Dropped off warranty book and collected credit card,
Installed a 5 ton Platinum 20 upflow system that serves living room.
Job walk and scheduled for Jonny to install customer supplied ceiling fans Monday 8am sharp
Hydes will Contact Angelo so that he contacts our client for scheduling drywall repairs. Hydes will cover cost.With the American Standard system for the master bedroom closet. I lowered the CFM to 350 for air circulation. I made the condensing unit and system only run in low speed. System was cycling too much and creating way too much humidity. Mrs Cook will be monitoring the system and letting me know if this works for her.Mrs Cook will cut a check today once line sets are complete for $6440.
Adding second system to comfort plan check cooling components for both system on the roof working properly
I performed a maintenance on (2) cooling systems and I found that the living room system was (2) pounds low on R-410a Freon and I recharge the system and tested. I advise client that there is a possibility of a leak in the system. Then I changed out (2) filters located on the ground
Connected the system so that our client will have cool air until we replace the line set on Thursday She will pay in full once job is completed
D Performed a semi annual cooling service on four split system Refrigerant checked out OK Electrical checked out OK Compressor checked out OK v Condensing fan motor checked out OK Contactor checked out OK Capacitor checked out OK Thermostat checked out OK Cleared condensation lines with CO2 Rinsed condensing unit out with H2O Rinsed the filters located within the FAUsWe are performing an isolation test on the common area unit I will be back to the property On June 19 to check results.
Quoted on a Daikin Ductless
Performed an isolation test Please schedule between 630 to 730 Wednesday
Living area low refrigerant. Made client aware of leaking system. Mostlikly slow leak.
Hooked up to 240 V Esso cord to a 240 V spider box
Bad condenser fan motor, client to call back if she decides to replace equipment.
Performed ac service on all 3 package systems. All within man. Spec. Cleared condensation line and condenser coils.
Preformed annual service on 3 units Changed filters, checked capacitor, amps, Freon levels and washed condenser coils
Upon arrival found your rooftop package unit on responsive to commands from thermostat. With further inspection we discovered the inner workings of the disconnect box or fried and very brittle. Installed new 60 amp disconnect box and cycled system. System is now operating and cooling properly.
Upon arrival I found the living room unit flat on refrigerant We will be doing an isolation test June 17