Hyde’s promises customer service that exceeds the expectations of Indian Wells CA residents.
Call us now at: (760) 360-2202. We’d love the opportunity to earn your business as we have with your neighbors in Indian Wells CA.
for Indian Wells, CA
Our Reviews by City
Siu - Indian Wells, CA
friendly and helpful
Very courteous]. Thorough. Excellent work
Richard - Indian Wells, CA
Hyde's customers to be happy & pleased. Good people. Jonathan has always done a good job for us. Thank you, Jonathan. In fact everyone we have met at Hydes is first rate.
Christine - Indian Wells, CA
From the initial call until job completion, the team was effective and efficient.
Frank - Indian Wells, CA
Your technician Casey was very knowledgeable and also informative as to what my issues were with AC units, he took the time to explain what the problem was that we could understand. I would certainly ask for Casey for any future issues with my AC.
Bill - Indian Wells, CA
Always professional and pleasant
Paul - Indian Wells, CA
Five star servicer
Dave - Indian Wells, CA
Friendly and foodservice
Richard - Indian Wells, CA
Great service from Greg
Paul - Indian Wells, CA
Winnie - Indian Wells, CA
Greg gave me a heads up when he was on his way. He was professional, knowledgeable, and quickly diagnosed and repaired the issue.
Set minimum airflow to 40%. Also cleaned outdoor unit to get ready for winter
I performed a maintenance on (1) cooling system and I found that everything checked out ok. Then I changed out (1) filters and flushed out the condensation drain located on the ground
Installed a 4 ton Platinum 18 POV Upflow Split Heat Pump System with sensor in bedroom.
Wash both condenser check cooling components working properly
System is operational client installing unit next week. Forgot to close call I was only there for 30 minutes
Estimate to install a 4 ton American Standard Silver 14 condensing unit and coil in downflow position.
Install filter at furnace 20/25/5 Client has paid
Sold for Saturday
Installed an American Standard Silver 15 split heat pump system.
Honeywell 8000 thermostat and wireless condenser module lost connectivity. System is now reconnected and operating properly.
Installed a 100,000 btu furnace only.
Bad capacitor. Replace and gave client est on replacement. Will credit repair 194.00 if done within 2 weeks
Upon arrival client stated ac not working. Client stated he talked with tech last night and tech advised him on Edison box. Advised if Edison box at the condenser has a sold green light that means Edison has turned the system off. Tech advised Edison should only have the box off between 5-9pm. Upon arrival found Edison box still calling for the unit to be turned off. Removed Edison box from low voltage and cycled system. Found systems compressor not turning on. Checked capacitor and capacitor still within range. Checked add on item call the hard start kit which helps start up the compressor and found that to be bad. The compressor shouldnâ€™t need a hard start kit to run. Removed old start kit and installed new hard start. Cycled system and compressor turned on. System is 1996. System is well past life expectancy. Tenant payed for repairs today and tech will call homeowner and advise on issues.
Upon arrival client stated bedroom system not working. Found dual run capacitor rated for 30/7.5 completely dead. Replaced capacitor and cycled unit. Client has already sold the house. Capacitor under parts but not labor warranty.
Found breaker tripped again. Made Client aware that he needs to do the panel tuneup also possibly split up air conditioners on separate circuits. There was a time delay for second stage in the bigger unit I swapped it to delay the first stage call for when the unit comes on so they both donâ€™t come on at the same time. Courtesy for cust.
Preformed a semi annual cooling service on two 2015 American Standard split systems. Cleared condensation drain line and changed 20x25. 16x25 filters at furnace/ garage. 3 and 4 ton condensers are located on ground. Cycled system checked capacitor, compressor/ fan motor amps and voltage. Secured and cleaned electrical at condenser. Checked refrigerant sub cool, super heat and line temp. Cleared condensation drain line. Thermostats checked out ok. Rinsed condenser coils. Equipment checked out operational at this visit. Recommended Re-Ducting the whole house. Found collapsed duct. Very little attic space. Homeowner will schedule in December for estimate.
Preformed a semi annual cooling service on three cooling systems Trane 2013. Amana Changed 20 x 30 x 1, 20 x 20 x 1, 16 x 16x1. 14 x 14 x 1, 12 x 24 x 1. filters throughout the house. Condensers are located on ground. Cycled system checked capacitor, hard start kit, compressor/ fan motor amps and voltage. Secured and cleaned electrical at condenser and fuse box. Checked refrigerant sub cool, super heat and temperature split/ R22. Cleared condensation drain lines. Thermostats checked out ok. Rinsed condenser coils. Equipment checked out operational at this visit.
Upon arrival client stated system blowing warm air. Found no power to condenser. Found breaker half tripped. Found compressor capacitor completely dead. Installed new capacitor and reset breaker. System is working properly.
Had to reset breaker. One breaker for two air-conditioning systems. Client needs main panel tuneup or more see estimate
Performed annual AC maintenance. Changed two 20 x 30 x 1 and three 14 x 14 x 1 filters. Checked amps, volts, capacitors and all other electrical problems within a system. Checked refrigerant levels, superheat, sub cooling temperature split and refrigerant level to be with the manufacture specifications. Both systems are operating and cooling properly at time of service.
Found system operational upon arrival. After evaluation I found it lacked maintenance and was 3 pounds low on our 410 a. I replaced a 20 x 25 filter cleaned condenser coil. See picture of gauges. High superheat indicates possible issue with metering device.We decided to see how it will do. If problems persist replace 5 ton 410 A expansion valve. See est.
MIke left message for customer. Left cell number for him to c/b.
Did maintenance on two 2016 American Standard platinum units, furnace is located in attic, condensation termination located at sink of garage bathroom, checked all electrical components and refrigerant levels superheat, sub cool, temp split, all are within manufacture specifications. Both systems are cooling and operating properly at time of maintenance.