HVAC Repair & Electrical Services Near Palm Springs, CA
Since 1972, Hydes Air Conditioning has been providing HVAC services including repair, installation and maintenance to residents in Palm Springs. We've also added electrical services to our family of home services to better serve our community. Hydes is proud to be your preferred local service provider for all your HVAC and electrical needs.
Home AC Repair Service
When it comes to AC repair, installation, maintenance and tune-ups, there’s no better company to call than our team of N.A.T.E. certified HVAC experts near Palm Springs, CA. We’re highly experienced in all things related to your home air conditioner and heating system, so whether your air conditioning unit isn’t cooling your home or you need routine maintenance service, don’t suffer in the heat – give us a call today!
We also offer Indoor Air Quality solutions to keep your home’s indoor air clean and make sure you and your family are not breathing in unwanted pollutants.
Palm Springs Electricians
Hydes is a full-service electrician company servicing the Palm Springs, CA area. We'll handle all of your electrical repair needs, including:
- Electrical Panel change-outs & upgrades.
- Smoke alarm and CO2 safety checks.
- Indoor & LED lighting.
- Patio & landscape lighting.
- Whole home generators.
- Safety inspections and checks.
- EV charger installation.
Standby Generac Generator Installers
Palm Springs residents know the importance of being prepared for power outages. That’s why many homeowners are investing in whole home generators. Hydes generator installation service offers you and your family the best solution. As certified Generac dealers, we provide customers with high-quality standby generators that automatically kick in the moment power is lost.
In addition to new installation, we also offer repair and maintenance services for existing generators. With a backup generator in place, homeowners have peace of mind knowing that their home will have power even when the grid is down.
HVAC & Electrician FAQs
It costs around $3,500-$8,000 to replace an air conditioning unit in Palm Springs, CA. Price will vary based on several factors:
- The size of your house.
- The type of air conditioning unit you have installed.
- The cost to remove your current AC unit.
Getting your current air conditioning unit replaced is a good way to improve the climate control in your home and also cut down on energy and repair costs.
Your AC unit may be running but not cooling your home in Palm Springs, CA because:
- Your air filters are blocked
- Your AC unit has a refrigerant leak
- Your evaporator coil is dirty or frozen
If your AC unit is running but not cooling your home, there may be a deeper issue going on with your air conditioner. If you replace your air filters and set your thermostat correctly and it is still not working properly, you should have an HVAC technician repair your AC unit.
The average cost for LED lighting in Palm Springs is $100-$150 per light fixture. The price largely depends on:
- The number of light fixtures you want
- The type of light fixtures you want
- The number of watts you will need
LED lighting lasts longer and uses less energy so you save on your monthly energy costs!
Minor HVAC repairs, such as fuses, breakers or thermostat replacement, cost between $150 and $290. You can expect to spend $200 to $1,500 on substantial repairs such as repairing a refrigerant leak or evaporator coil.
Additional heating and cooling repairs will increase the cost, but keeping your furnace and central air conditioning system in good working order will save you money in the long run. The cost of air conditioning repair will also vary depending on the size of your home and the brand and type of heating and cooling system you have installed.
For simple tune-ups, regular AC maintenance costs $75 to $200. Extended service contracts range from $150 to $500 and cover the entire HVAC system, including heating and cooling.
Maintenance calls typically include cleaning the condenser and performing a series of checks to ensure that your system is operating properly. We'll also look for other repair and maintenance issues. Standard AC tune-ups do not usually include evaporator coil or duct cleaning.
The best time to have AC maintenance done is in spring, but if your air conditioning tune-up was overlooked, you can have it done anytime during summer to improve your AC’s performance.
The average cost of a small electrical job is $140 to $420. Larger jobs can range from $1,600 to $10,000 or more. To save money, make a list of all the electrical work that needs to be done in your home and have it completed in one or two visits. Other electricians typically charge $40 to $100 per hour and a $75 service call-out fee. Hydes charges by the job, not the hour.
Local Electrical & HVAC Providers You Can Trust
We’d love to earn your business in Palm Springs, CA! See what your neighbors are saying about our electrical and HVAC installation, repair and maintenance services below.
for Palm Springs, CA
Our Reviews by City
As per Usual, Great Service
Joseph - Palm Springs, CA 92262
Great Service. You sense that as a customer, you count.
Excellent Service and Professionalism
Dan - Palm Springs, CA 92262
Arlle - Palm Springs, CA 92264
Fast, personable, friendly. Good to see him again.
Jean - Palm Springs, CA 92264
Brian is a courteous efficient young man who explained everything he was doing. He asked if I had any questions and made sure that I was satisfied. Enjoyed meeting him
Response from Hydes Air Conditioning:
Thats so wonderful, thank you!
Justin - Palm Springs, CA 92262
Lois - Palm Springs, CA 92262
Jeff is a very nice & knowledgeable person. He was very patient & helpful in answering several questions that I had.
Doug - Palm Springs, CA 92264
The service was very professional and friendly . Jeff is always courteous.
World Class Service!
Carol - Palm Springs, CA 92264
Hyde’s is ALWAYS wonderful, when they come out! Office Staff equally wonderful, when scheduling appointments.
Justin - Palm Springs, CA 92262
Justin - Palm Springs, CA 92262
Bob - Palm Springs, CA 92264
Mark - Palm Springs, CA 92264
Great service check up. On time, courteous and knowledgeable. Thank you
Holly - Palm Springs, CA 92262
He was great helping me over the phone. No charge.
Very Good Service
Lois - Palm Springs, CA 92264
The technician was very knowledgable and explained everything in terms that I could understand
Sebastian - Palm Springs, CA 92262
Knowledgeable. Friendly. Polite and Fast.
Molly - Palm Springs, CA 92262
Justin - Palm Springs, CA 92262
James - Palm Springs, CA 92262
Alex provided thorough and excellent service. It was perfect in every way.
Rose - Palm Springs, CA 92262
As always Alex was both friendly and competent. Excellent as always!
Elaine - Palm Springs, CA 92264
Alex was great!
Hyde’s is always First Rate
Duane - Palm Springs, CA 92262
Jeff is very friendly and explains what he’s doing
Ron - Palm Springs, CA 92264
He did a fine job of changing the oil. I don’t think he change the air filter and the price of $250 for a little oil change is ridiculous. I paid $100 for my Acura and they change the oil filter and rotate the car tires.
Response from Hydes Air Conditioning:
Hi Ron I confirmed with Nick and he did change the filter and spark plugs during his comprehensive annual inspection & maintenance on your whole home generator. Your neighbor actually negotiated for a lower price for you both since we did them on the same day and commented on what a great deal he thought it was. I am sorry to hear that you did not feel the same. We will defintely work on showing you the value of our service the next time we are out.
Phyllis - Palm Springs, CA 92264
Technician showed up on time and completed the service in a timely manner
David - Palm Springs, CA 92264
Hydes air conditioning and heating are the best
Michael - Palm Springs, CA 92262
Everyone from the office staff to the technician coming out and repairing my heater. They all had a great customer service qualities and professional.
Emailed revised quotes
Performed annual cooling maintenance on a 2019 American Standard Gold 3 ton split system. FAU located in outdoor closet. Rinsed washable filter located in FAU. Condenser is located on the ground behind the house. Followed sequence of operations and checked voltage, amperage, FLA, RLA, LRA, capacitor, 2-stage rectifier, temperature split and cleared condensation line from FAU. Found compressor LRA to be close to over amping manufacture specifications at 80/83. Informed and recommended Hard Start Kit to reduce amperage at start up to prevent damage to the compressor and to also prolong the life of it. Sent estimates via email. Rinsed condenser coil. Everything checked out in range. Ecobee thermostat checked out operational. System is working at manufacture specifications in cooling at this time of service.
2014/. 2.5 ton Performed a semiannual cooling service on American thunder split heat. Replaced 16 x 25 filter located within the air handler/hallway mechanical closet. Condenser located on ground. Cycled equipment followed cooling sequence of operation checked capacitor, hard start, compressor, fan motor, amps and voltage. Check refrigerant/temperature split. Cleared condensation line. Rinsed condenser coil. Cooling equipment checked out operational at this visit.
Remove old hook ups for ACs. rerun mini split to main panel, approx 50 ft. Add ground rod to garage sub panel. Add ground busbar to garage sub panel.
10+system 14/20 14/24 check cooling components everything is working within manufacturing specifications
Performed annual maintenance in cooling on a 2022 5 ton American standard heat pump, followed sequence of operation cleared condensation line checked amps voltage capacitor temperature split working at range, changed filter rinsed condenser down, condenser working to manufacture specification in cooling
Performed annual maintenance in heat on a 2022 5 ton American standard heat pump, followed sequence of operation changed filter cleared condensation line checked amps voltage capacitor temperature split working at range, condenser is working to manufacture specification in heat
Performed annual cooling maintenance on a 2019 American Standard Platinum 4 ton split system. Replaced 20x30 filter located in hallway ceiling. Followed sequence of operation and checked voltage, amperage, Freon levels, temperature split, found no error codes on CDA and cleared condensation lines. Everything checked out in range. Thermostat checked out operational. Rinsed condenser coils. System is working at manufacture specifications in cooling at this time of service.
Bill Lansman John Stewart Quoted on a American Standard
Performed annual cooling maintenance on a 2017 American Standard Gold 5 ton Split System. FAU is located in indoor closet. Replaced customer supplied accuclean filter. Followed sequence of operations and checked voltage, amperage, LRA, FLA, RLA, capacitor, hard start kit, 2-stage rectifier and temperature split. Everything checked out in range. Rinsed condenser coil and cleared condensation line from FAU. Condensate pump checked out operational. Thermostat checked out operational. System is working at manufacture specifications in cooling at this time of service.
20/25 check cooling components everything is working within manufacturing specifications temp split 20
Performed annual cooling maintenance on two 2015 and 2016 American Standard Platinum 3 ton and 4 ton units. Replaced 16x30 filter in hallway ceiling and rinsed washable filter located in garage FAU. Followed sequence of operations and checked voltage, amperage, cleared condensation lines, temperature split and checked Freon levels with CDA. Found no error codes on CDA. Rinsed both condenser coils. Both 1050 thermostats checked out operational. Both system are working at manufacture specifications in cooling at this time of service.
Run wire for dedicated circuit for 3 electric heaters on patio, pull from sub panel to patio
20/25 check cooling system replace 20/25 filter everything is working within manufacturing specifications
I performed a maintenance on (1) heating system and I found that everything checked out ok. Then I change (1) filters and I flushed out the condensation drain located on the ground (1)2017 model
I performed a maintenance on (1) heating system and I found that everything checked out ok. Then I change out (1) filters located on the roof I also performed a maintenance on (1) cooling system and I found that everything checked out ok . Then I flushed out the condensation drain located on the roof (1)2014 model
Replaced all accessible ductwork for basement system. Maintenance program with 15% discount. We removed all ductwork, ordered the new ductwork and will return tomorrow to install new ductwork so electricians can finish their work.
Repair wiring for floor plug. Warranty. No charge.
Quoted on a American Standard and York package unit
I cleaned the condenser coil and I cleaned out the filters on the dual zone mini split and then I tested the heat cycle. I was getting (120) degrees out of the living room indoor head and (119) degrees out of the bedroom indoor head . Then I changed out the batteries on both the mini split remote with client supplied batteries and tested. The system is working good at this time
Per client didn’t replace filter client did it last week check cooling components everything tested within manufacturing specifications 10+ years system added compressor kit tested
Add two brass floor plugs. Add one surface mounted light fixture to existing fixture. Sub panel tune up