Top Rated Electrician & Air Conditioning Repair Services – Palm Springs, CA
Hyde’s AC has been providing HVAC services to residents in Palm Springs since 1972. We now offer Electrician services.
Call us now at: (760) 360-2202 for all your HVAC service needs and see what your neighbors are saying about our air conditioning and heating service below.
We’d love the opportunity to earn your business as we have with your neighbors in Palm Springs CA.
for Palm Springs, CA
Our Reviews by City
Bruce - Palm Springs, CA
Danny and team did a great job we’re very informative and explained everything they were doing and did in detail so we understood. Awesome service as always
Nancy - Palm Springs, CA
Ed - Palm Springs, CA
On time. Fix in place in 45 minutes
Brian - Palm Springs, CA
John - Palm Springs, CA
Casey knew what he was doing and explained everything.
Robert - Palm Springs, CA
Van - Palm Springs, CA
Hydes is great.
Lynn - Palm Springs, CA
Amador was terrific...very helpful and considerate. It was a pleasure to have him in my home.
Julie - Palm Springs, CA
They’ve been our go to company while living in the desert. Always responsive and same day service most of the time.
Tina - Palm Springs, CA
I just wanted an overview on replacing my aging units but was not ready to move forward. Barry offered me some advice about replacement ( or not..)
Rooftop, check heater system working properly 24/24 fiiter
Comfort heater service on two 2016 American standard split systems. Fau located inside the garage and bedroom closet attic. Replaced and washed filters. Checked all heater components, static pressure, volts, amps and safety switches. Installed water safety switch in system in the attic. Reconnected thermostats to WiFi and client phone. Reset filter timers.
Service heating furnace located back of home in outside closet Heating is per manufacture specification temp rise equals OK CO test because OK inform client that unit is past life expectancy he is aware of furnace age unit is operating safely
Condenser fan motor not running upon arrival inspection revealed faulty dual run capacitor reference 45 and 5 fan side reading zeroâ€”-fan not damaged running under rated amps recommend service plan not at this time not at this time
Performed heating maintenance. Cleaned blower compartment and blower motor. Flushed out condensation drain line. Checked sequence of operation and temperature rise system is running at factory specifications. Recommended condensation safety switch client is interested and will contact office once a decision is made.
Service heating furnace is located in garage filters located in the home furnace is heating per manufacture specification blower speed correct condensate line cleared termination side of homeâ€”Flame rectification numbers good reference what was it 5.7 â€”-did recommend water safety switch client not interested at present time Client interested in remote comfort controller sent estimate Client said he needs a little time to think about it please call office when you want us to install this
Performed heater service. Package unit. Marked unit 251. System operational. 20x20 filter
We will be out on Wednesday, February 19 to perform a panel tuneup.
I performed a maintenance on (2) heat pump and I found that everything checked out ok. Then I changed out (2) filters located on the roof
Performed heating service on 1 system. Dialed in airflow. Replaced filter. Set up low heat and cooling fan to 1600 cfm in high cool.
Pulled blower and cleaned. Also sprayed down coil with no rinse coil cleaner. Upon checking operation of the ac I found low voltage to main power. Upon checking panel found low voltage at the main breaker. When I went to reset main it would not. Client is calling his electrician.
I found that the pressure in the evap coil has dropped and that there is a leak and I recommend replacing the evap coil . I found that the pressure on the condenser stayed where I had left it however I see oil on the condenser coil
I performed a maintenance on (1) heating system and I found that everything checked out ok. Then I changed out (1) filter client supplied the filter and I flushed out the condensation drain located on the ground
We will be disassembling the 4 inch recessed lights in the living room. Replacing the guts with new guts. This will consist of the heat sink and sockets. We will supply the client with 18 par 20 LED lamps
Installed a two pole Federal Pacific breaker. Installed a weatherproof GFI
Service heating furnace is located on the roof package unit â€” Furnace is heating per manufacture specification â€”â€”clear condensate line â€”â€”all heating electrical within manufacture specification â€”apartment complex need long rope (for equipment haul to roof) ladder for roof access is in parking garage
We will install a two gang cut in box for the lighting over the fireplace. We will install 120 V receptacle behind TV.
Jonny and SERGIO are in route to install a circuit for TV and install a box for switches
Marry cancel service she will call Hydeâ€™s to make another appointment
System installed 2018 4 ton package heat pump. System operational and within manufature specification. Thermostat hard to press buttons. Filter 14x46.
Check heater system working properly replace 24/24 filter gave Starbucks card
Performed a semi annual heating service on 2016 American Standard Split system. Furnace is located in outdoor closet. 5 ton condenser is located on ground. Changed 20x25 filter located at furnace. Followed sequence of operation and checked volts, amp, heating safety switch, water safety switch and temperature rise. Cleaned out burners, electrical and furnace. Cleared out condensation drain line. Thermostat checked out ok. All heating components checked out according to Manufacturers Specifications. Outer drywall has organic growth. I opened up return register and didnâ€™t see anything growing in the inside of platform. Installed Honeywell UV light with odor absorption to deactivate airborne and surface contaminants like mold, bacteria and viruses for both coils and air treatment.
Performed a semi annual heating service on 2018 American standard Heat pump Air handler is located in hallway closet. 3 Ton condenser is located on ground. Changed 16x20 filter located on lower wall. Followed sequence of operation and checked volts, amps and reversing valve. Cleaned out electrical, cleared out condensation drain line/ was unable to find condensation termination. Thermostat checked out ok. Equipment checked out operational at this visit
I performed a maintenance on (1) heating system and I found that everything checked out ok. Then I changed out (1) filters located on the roof
I performed a maintenance on (1) heating system and I found that everything checked out ok. Then I changed out (1) filters located on the ground