Electrician & Air Conditioning Service Reviews – Indio, CA
Hyde’s Air Conditioning & Heating promises customer service that exceeds the expectations for Indio CA residents. Since 1972, thousands of families and business owners have trusted Hyde’s to install, maintain and repair their air conditioning and heating systems. We now are offering Electrical Services.
Call us now at: (760) 360-2202 for all your HVAC & Electrician service needs.
We’d love the opportunity to earn your business as we have with your neighbors in Indio CA.
We are located at 42949 Madio St, Indio, CA 92201.
for Indio, CA
Our Reviews by City
Marcie - Indio, CA
Great service during Covid 19 epidemic
M - Indio, CA
Great staff, technician and service
Helen - Indio, CA
Promo courteous and thorough service
Wally - Indio, CA
Danny clearly explains everything he did.
Vernadine - Indio, CA
David - Indio, CA
Casey was very knowledgeable guy. He explained the difference in units.
My Air conditioner!
Pat - Indio, CA
Amador was awesome! Very respectful, knowledgeable and most of all very professional. He is the only one I want to take care of our equipment. Thank you again Amador!
Steve - Indio, CA
William - Indio, CA
The men came on time and completed the job very efficiently.
John - Indio, CA
Service on 1 system. Cleared condensation line and condenser coil. System within manufacture specification. Replaced filters
Performed ac service. System operational but beyond life expectancy. R22 system. Low dual cap. Replaced and added starting capacitor.
Performed cooling maintenance and safety check. Replaced all filters inside home, Cleaned outdoor condenser coilâ€™s and electrical compartments. Checked run capacitorâ€™s are good and within range. Check the start up amps in running amps. Suggest installing start capacitor and compressor saver Kit to assist with LRA starting amps. Verified refrigerant charge is good and within range. Equipment is working properly at this time.
Performed ac service on 1 system. Replacing equipment.
One time tune up on r22 split system. Fau located inside the attic. Replaced filter in hallway. Cleared lines and washed coils. Checked all ac components, Freon levels, volts, amps and capacitors.
Perform cooling maintenance and safety check. Upon arrival noticed condenser fan motor not working checked dual run capacitor and found it to be bad. Install two dual run capacitorâ€˜s and checked amps. Verified refrigerant charge is good and within range, Verified all electrical is tight and secure. ReplaceD two 20 x 30 x 1â€ filters, washed outdoor condenser coilâ€™s. Equipment is working properly at this time.
I Performed Maintenance on both of the Cooling Systems. Also checked a 20x30 and two 14x24 filters. Both Cooling Systems are 2010 models located on the ground. I balanced the Subcool to 9 Degrees for the 4 ton Living Room System and tested the system. Everything else checked out operational at the time of service.
We will install a dedicated circuit from meter main panel to the exterior barbecue. We will replace three GFIâ€™s. We will replace a switch and surface mount light fixture. We will repair the GFI next to pool equipment and remove the time clock.
Performed ac service on 1 system. Operational and within manufature spec. Cleared condensation line and condenser coil.
I Performed Maintenance on the Cooling System. Also replaced a 20x30 and 14x14 Filters. The system is a 2013 model located on the ground. I also flushed the condensate drain. Everything else checked out operational at the time of service.
Performed cooling maintenance and safety check. Replaced 20 x 30 x 1â€ filter located in the home. Flushed condensation drain line inside the attic. Washed outdoor condenser coil located on the right side of the home. Verified all electrical is tight and secure. Verified amp draw and run capacitor are good and within range according to manufacturer specifications.
Performed ac maintenance on (2) 2019 American Standard split systems w/ 1050 thermostats. Changed 20x30 and (2) 14x24 filters located in house ceiling. Cleared condensate drains. Cycled units on second stage cooling. Found system pressures to proper refrigerant charge and line temperatures. Compressors, fan motors, and capacitors were working to specification.
Performed ac maintenance on r410a outdoor unit. Homeowner changed filters I left at front door. Cleared condensate drain. Cleaned outdoor coil. Compressor, fan motor, and capacitor were working to unit specifications. Found unit low on Freon (Superheat 45; subcool OL). Added 3 lbs of refrigerant with homeowners request. Got Superheat to 15 and Subcool to 8-9). System was working properly at time of service.
Wash condenser check cooling system cooling properly
Comfort ac service on American standard platinum split system. Fau located inside master bathroom attic. Washed filter that is located at the fau. Checked Freon levels, cleared lines and washed coils. Advised on indoor air quality products.
Performed ac maintenance on 2 york condensing units. Cleared condensate drains and cleaned outdoor coils. Changed 20x30 and (2) 14x24 filters. Both system preasures and line temperatures were to specification. Compressors, fan motors and capacitors were working properly. Cleaned mini split filters and outdoor coil. Mini split was working properly at time of service.
Comfort ac service on 2013 and 2018 American standard split systems. Fau located inside laundry room attic. Replaced filters throughout the house. Checked all ac components, Freon levels, volts, amps and capacitors. Cleared lines and washed coils. Found 2013 units run capacitor outside itâ€™s range. Rated 45 and was reading 39.6. Replaced capacitor under parts warranty. Recommended hard start kits to increase the life of the compressors.
Performed ac maintenance on 2017 Lennox condensing unit. Cleared condensate drain and cleaned outdoor coil. Changed 20x30 and 20x20 filters. System gauge pressures and line temperatures were to specifications. Compressor, fan motor, and capacitor were working properly.
I Performed Maintenance on the Cooling System. Also left 20x30 outside front door per client request. The system is a 2019 model located on the ground. Everything else checked out operational at the time of service.
Service 3 system 5 ton system very low an refrigerant , customer will call home warranty, casita system added 1 pound of r 22 Recommend replacement
Performed cooling maintenance and safety check. Replaced two filters inside home. Washed outdoor condenser coil, verified all electrical is tight and secure, verified run capacitor is good and within range, check running and start amps are good and within range. Equipment is working properly at this time.
Wash condenser check cooling system cooling properly
Preformed a semi annual cooling service on 2018 American Standard Split system. Furnace is located in garage. 5 ton condenser is located on ground. Followed sequence of operation and checked capacitor, Compressor/ fan motor amps and voltage. Secured and cleaned electrical at condenser and fuse box. Checked R410A levels sub cool, super heat and line temp. Cleared condensation drain line at furnace Rinsed washable filter/ furnace. Rinsed condenser coil. Thermostat checked out ok. Equipment checked out operational at this visit