Electrician & Air Conditioning Service Reviews – Indio, CA
Hyde’s Air Conditioning & Heating promises customer service that exceeds the expectations for Indio CA residents. Since 1972, thousands of families and business owners have trusted Hyde’s to install, maintain and repair their air conditioning and heating systems. We now are offering Electrical Services.
Call us now at: (760) 360-2202 for all your HVAC & Electrician service needs.
We’d love the opportunity to earn your business as we have with your neighbors in Indio CA.
We are located at 42949 Madio St, Indio, CA 92201.
for Indio, CA
Our Reviews by City
Great service as always!!
Elaine - Indio, CA
I love Hyde’s AC! Service and techs are extremely reliable and trustworthy!
Anne - Indio, CA
Both techs were professional. They arrived on time. Courteous & friendly.
Great service again!
Edward - Indio, CA
Luis was great and fixed everything we needed
Donald - Indio, CA
Great price and installation
Tom - Indio, CA
All work was done efficiently and area cleaned up
Pleased with his service and knowledge. Jonathan is a good asset and respresentative of Hydes.
Kryn - Indio, CA
He did very well in explaining the gold and platinum systems we were interested in, so that we believe we made the right choice.
Dan - Indio, CA
Hydes A/C has been servicing our old A/C system for the past 9 years to our total satisfaction. The office staff and technicians have always been very polite and respectful and we have been very pleased with the maintenance on our system. Because of their excellent service we hired Hydes A/C to install a new A/C system for our home. We were pleased beyond words with each and every person that we dealt with throughout the whole process of explaining our many choices, prices, and then doing the installation. All of the employees were very pleasant and professional and did a top rate job of installing our Platinum 20 A/C unit. We could not be more pleased! We can highly recommend HYDES A/C! They are solid and honest business that will treat you right!
Michelle - Indio, CA
A very professional young man. Thorough and informative
Kevin - Indio, CA
The tech was great!
Jamie - Indio, CA
I would use this company again. My first call.
Heater service and safety check. Replaced filter, cleared drain lines from attic. 90% furnace with poor access to properly clear drain lines. Suggest two jones valves and water safety switch to properly clear condensation lines and protect home from potential water damage. Installed jones valves and water safety switch. Verified heater is working properly according to manufacturer specifications.
I found that the dual run capacitor was out of range and I replaced the capacitor and tested
Installed a 4 ton American Standard Gold 17 horizontal pov split heat pump system with two heating and cooling stages. Includes two IAQ products with installation, wifi thermostat. Limited time rebate from clean Air Furnace Rebate program. Needs breakers 4030s job completed
Replaced bulbs at address light and reworked transformer
Performed heating maintenance and safety check. Replaced filters inside home. Cleared condensation drain line from inside attic. Cleaned mechanical platform from excessive dust, cleaned out burner compartment. Verified Heating sequence of operation is working properly according to manufacturer specifications. Client is selling home and will wait to renew membership.
I found that the (1050) thermostat was malfunctioning and I replaced the thermostat and tested
Heating service and safety check. Replaced filters, cleared drain lines from attic. Checked temp rise 52, checked for signs of carbon monoxide. Verified all gas and electrical are tight and secure. Clean mechanical platform and burner compartment. Verified Heating sequence of operation is operational according to manufacturer specifications. Advised client of life expectancy here in the desert also advised that his systems refrigerant is no longer manufactured in the United States suggest replacing equipment to avoid costly inconvenient breakdowns.
Performed annual heating maintenance on 2019 Goodman 90% furnace located inside attic. Attic access is located inside master bedroom closet. Changed 20 x 30 x 1 filter. Checked amps, volts, capacitor for inducer draft motor and all other electrical components within the system. Checked all safety switches, static pressure and temperature rise. Also flushed condensation line and checked gas pressure. Recommend installing condensation water safety switch to prevent any water damage to the home or equipment due to condensation back up. Also recommend installing surge protector on system to protect vital components within the system from blackouts, power surges, faulty breakers and all other electrical failures that may occur and damage the system.
Panel tune up. 2 fan reciever
Comfort heater service on York split system. Fau located inside hallway attic. Replaced filters. Checked all heater and safety components. Capacitor rated 15 and reading 14.4. Client stated dust issues. Found another company had replaced txv and didnâ€™t seal the coil. Found coil open. Sealed coil and advised client.
I Performed Maintenance on the Heating System. Also replaced a 20x30 and 14x14 Filters. The system is a 2003 model located in the attic. I also flushed the condensate drain. Everything else checked out operational at the time of service.
Comfort heater service on split system. Fau located inside laundry room attic. Replaced filters throughout the house. Checked all heater and safety components. Capacitor rated 7.5 and reading 7.4. Showed client how to put thermostat off of program.
I Performed Maintenance on the Heating System. Also replaced a 20x30 and 14x14 Filters. The system is a 2011 model located in the attic. I also flushed the condensate drain. I advised client about adding a Water Safety Switch to prevent condensate drain backups from occurring. I also found that the blower motor run capacitor is rated for 7.5 and Iâ€™m getting 6.94 which is out of the plus or minus 5 percent range. Recommended replacing the blower run capacitor. Lastly I found that the Flue Pipe is falling apart and needs to be replaced. It is 4ft and 54 inches long. Took pictures of Flue Pipe for reference. Advised to client to NOT run Heater til we replace the Flue Pipe. Will get with one of the managers in the morning and get back to homeowner on price to replace it. Will send quote over for New Run Capacitor and Water Safety Switch.
I Performed Maintenance on the Heating System. Also replaced a 16x25 filter. The system is a 2008 model located in the garage. I also flushed the condensate drain. I found that the blower motor run capacitor is rated for 20 Microfareds and I was getting 16.34 which is below the 5 percent mark. I recommended and installed new Run Capacitor and tested the system. Everything else checked out operational at the time of service.
Estimate to replace leaking evaporator in attic. Completed replaced coil and charged system
Dropped off warranty book
Van inventory 12:30 -3:24
Did inventory and cleaned and organized van.
Attic check both heating system clean condensation line and heater burner check sequence of operations everything is working whiting manufacturing specifications
Performed furnace maintenance on 2018 new system in attic. All heating and electrical components were working properly. Zero carbon monoxide detected. Static pressure at return was 0.20â€wc. Changed filter and cleared condensation drain. Recommended water safety switch due to no protection currently on water drain from system.