Electrician & Air Conditioning Service Reviews – Indio, CA
Hyde’s Air Conditioning & Heating promises customer service that exceeds the expectations for Indio CA residents. Since 1972, thousands of families and business owners have trusted Hyde’s to install, maintain and repair their air conditioning and heating systems. We now are offering Electrical Services.
Call us now at: (760) 360-2202 for all your HVAC & Electrician service needs.
We’d love the opportunity to earn your business as we have with your neighbors in Indio CA.
We are located at 42949 Madio St, Indio, CA 92201.
for Indio, CA
Our Reviews by City
Maria - Indio, CA
Dale - Indio, CA
Great, efficient service, as we’ve come to expect
Mike - Indio, CA
Luci - Indio, CA
The presentation and explanation was thorough and helpful. Very happy to have gone with Hydes.
Rachel - Indio, CA
Excellent service. Quick and professional.
Tracy - Indio, CA
Hydes New AC Purchase and Installation
Ed - Indio, CA
We had our AC unit serviced which is 10 years old and there was an indication of a restriction in the system. We decided after being given three options to replace the system. At our install appointment day, the team showed up at 8:00am and worked in a very efficient manner to install our new system in 4 hours. We waited one week to allow the new system to operate. Its performing very quiet and efficiently compared with our old system. I would highly recommend Hyde's along with American Standard to anyone requiring a new coil and condenser. I had previously researched AC systems for our other home and American Standard was recommended by Consumer Reports. The price was also at a great value compared to my other home purchase. I highly recommend Hyde's for your service and if required new AC system install.
Robert - Indio, CA
We think he did a great job.
Frank did a very good job, on time, next and explained things to me very well. I would ask for him next time.
Barbara - Indio, CA
Tony - Indio, CA
Maintenance on cooling systems. Tested equipment and found everything running properly and within limits. Replaced filters, washed condenser coils and cleared condensation lines.
Replaced capacitor in both AC.
Client mentioned breaker tripping. Did not happen while was here. Tightened breaker and signed on maint. Program and performed. 20x30,14x14.
Quoted on a Ductless for guest bedroom
Maintenance on cooling system. Tested equipment and found everything running properly and within limits, replaced filters and cleared condensation. Washed condenser coil.
Performed ac service iid check me. System passed.
Performed comfort cooling services checked electrical wires and connections replaced filters clean drains checked Freon levels amps and motors. All AC operation are normal.
Maintenance on cooling system. Tested equipment and found everything running properly and within limits. Left filters for homeowner, washed condenser coil and cleared condensation line.
Perforemd service on heaters. Client want to add casita to the monthly. Change from 2 to 3 units. Bedroom system dosent work in heat. Needs new zone board. Possible other issues client not concerned.
Condenser coil dropped pressure, coil has been order.
Isolation of cooling systems and pressurizing with nitrogen. Did isolation on equipment, will order condenser coil and return to check other pressures.
Found compressor locked up. Tried to kick loose with start capacitor. Did not break loose. Tried 4 times. Client had general install equipment 2016. Told client to find out what labor warranty is from general and if itâ€™s up we can replace compressor under warranty. See est.
Performed ac service on 1 system. Low charge. Added 2lbs r22. See report.
Gave estimate on main unit and ductless for Casita.
Replace guard house filter 12/22 Bill job per office
â€œCheck meâ€ (1)â€”â€”system is r22 (condenser data plate)SYSTEM TO LOW TO TESTâ€”- unit has major refrigerant leak Low side PSI=3.3â€” high side PSI=77.3 System pressures too low to conduct check me â€”- system has refrigerant leakâ€” see notes
Maintenance on cooling system. Tested equipment and found everything running properly and within limits. Also installed Ecobee thermostat and tested. Left filter for homeowner, also washed condenser coil.
Quoted on 1.5 Ton Daikin Ductless for the garage. Line set outside wall , electrical underneath walk way. (Found Air Handler is 46 inches not 40. )
Performed ac service. Found system operational. Cleared condensation lines and condenser coils. System towards end of life expectancy.
Service cool -/ location attic and ground / USE AIR SPLIT FOR REFRIGERANT CHECK Client concerned about zoningâ€” live area gets too cool when guest bedroom is on â€”- ( office and live area are dump zones)â€”guest bedroom which is small should cool down before rest of home gets too coldâ€” will install one way curved blade in guest bed room 14/6( ref 75/70 ) Condenser is micro channel air split good at 23+ (69/46) Refrigerant Pressures and temps see photo and notes
Maintenance on cooling system. Tested split system, 2005 York model. Found system pressures ok and within limits. Also checked electrical and found dual run capacitor out of range, replaced and tested. Offered homeowner hard start kit but declined at this time. All other readings ok and within limits. Replaced filters, washed condenser coils and cleared condensation lines.
Performed ac service. Cleared condenser coil and condensation line. System operational. Coil was very dirty removed panels to clean.
Went over operation instructions.