Air Conditioning Repair Service & Electrician Reviews – Palm Desert, CA
Hyde’s AC promises customer service that exceeds the expectations of Palm Desert, CA residents for all your electrical, heating and cooling repair, installation and maintenance services. We’d love the opportunity to earn your business as we have with your neighbors in.
It costs around $350-$600 to repair and fix an air conditioner in Palm Desert, CA. The cost can vary depending on:
- How extensive the repair is
- The type of repair
- The contractor’s hourly rate
Another thing that can impact the overall cost of the repair is if it is on the weekend or after hours. A good way to cut down on repair costs is to get your air conditioning unit on a maintenance plan, as most maintenance plans offer discounts on repairs. To get your AC unit repaired or on a maintenance plan, call us today.
Some of the benefits of a heat pump in Palm Desert, CA include:
- It uses less energy each month
- It has a longer service life
- It is more eco-friendly
To find a good electrician in Palm Desert, CA, you should:
- Check online reviews and ratings
- Ask coworkers and friends for recommendations
- Ask electricians if their workmanship is warrantied
Most reputable electricians will have a warranty on their workmanship in the case that you experience an issue with a repair or an installation later on. Additionally, you should always ensure that the electrician you hire is licensed and insured to perform work in your state. To find out more about our electrical services, contact us today.
See what your neighbors are saying about our electrician, heating and air conditioning repair services below.
for Palm Desert, CA
Our Reviews by City
James - Palm Desert, CA
Installation was efficient; Josh demonstrated his experience and knowledge.
Donna - Palm Desert, CA
Jeff arrived on time. Knowing that I recently purchased the property, Jeff took explained things about the system with which I was not familiar. He completed the inspection and gave me a report.
Don - Palm Desert, CA
Just signed up for my fifth year.
Donna - Palm Desert, CA
The tech was on time and was very polite, Explained what the service included and what he would be doing
Professional, efficient service.
Carl - Palm Desert, CA
Jeff is great! Friendly, professional, quick and efficient. This man is a keeper.
Excellent and Professional
Georgia - Palm Desert, CA
Semi Annual Service
Dan - Palm Desert, CA
On-time and efficient. What I have come to expect from Hyde's.
AC Unit Replacement
Roy - Palm Desert, CA
The team did a great job on the installation of the replacement unit. They left the garage area neat and clean. They are able to answer any questions that I had. Will use Hydes AC and the same technicians in the future.
Ron - Palm Desert, CA
Bonnie - Palm Desert, CA
Taylor was very thorough & attentive to our issues. He answered all of our questions & was very personable!
Faulty circuitboard â€”-(Power going into the board but not powering blower motor â€”â€”Tested motorâ€”- motor is running properly)â€”-Will need to order board on Mondayâ€”-I will call client On Monday with board statusâ€”â€” Install temporary relay control for cooling only â€”-Test relayâ€”Relay is working properly system turns on and off with thermostat control
I Performed Maintenance on both of the Cooling Systems. Also replaced two 20x30 and a 20x20 Customer Supplied Filters. Both Cooling Systems are 2018 and 2010 models located on the ground. I also flushed the condensate drains. I advised client that the Dual Run Capacitor for the 2 ton unit is reading slightly out of range. Everything else checked out operational at the time of service.
Dryer access door panels.
Assist Amador see Amador dBrief Faulty Dual run capacitor fan side (replaced) Faulty high limit ( bypassed) System is two stage cooling micro channelâ€”-Y2 not hooked up at package unitâ€”â€”-26 template split â€”-checked in first stage cooling (probably why temperature split is so high due to blower speed )
High limit switch was bad not allowing contractor to engage also replace condenser fan motor tested operations checked temperature split and re-wired bipolar IAQ everything is working at this time.
Performed cooling maintenance on 2019 American Standard split system. Furnace located in attic/access second floor door. Changed out 20 x 25 x 1 filter. Upon maintenance found hi side of pressures and sub cool climbing, recovered refrigerant and numbers now stabilized. Will mon